(a) Ignitable or reactive waste must not be placed in a tank system, unless:
(1) The waste is treated, rendered, or mixed before or immediately after placement in the tank system so that:
(ii) Section 265.17(b) is complied with; or
(2) The waste is stored or treated in such a way that it is protected from any material or conditions that may cause the waste to ignite or react; or
(3) The tank system is used solely for emergencies.
(b) The owner or operator of a facility where ignitable or reactive waste is stored or treated in tanks must comply with the requirements for the maintenance of protective distances between the waste management area and any public ways, streets, alleys, or an adjoining property line that can be built upon as required in Tables 2-1 through 2-6 of the National Fire Protection Association's “Flammable and Combustible Liquids Code,” (1977 or 1981), (incorporated by reference, see § 260.11).