e-CFR Navigation Aids Advanced Search — Boolean
Related Resources |
## Electronic Code of Federal Regulations
Title 10: Energy
## §429.59 Pumps.(a) Determination of represented value. Manufacturers must determine the represented value, which includes the certified rating, for each basic model by testing (which includes the calculation-based methods in the test procedure), in conjunction with the following sampling provisions. Manufacturers must update represented values to account for any change in the applicable motor standards in §431.25 of this chapter and certify amended values as of the next annual certification. (1) Units to be tested. The requirements of §429.11 are applicable to pumps; and for each basic model, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any value of the constant or variable load pump energy index or other measure of energy consumption must be greater than or equal to the higher of: (A) The mean of the sample, where: and x̅ is the sample mean; n is the number of samples; and xi is the maximum of the ith sample; Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where: and x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95 percent one-tailed confidence interval with n-1 degrees of freedom (from appendix A to subpart B of part 429); and (ii) Any representation of weighted energy factor of a basic model must be less than or equal to the lower of: (A) The mean of the sample, where: And x̅ is the sample mean; n is the number of samples; and xi is the maximum of the ith sample; or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.95, where: And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95 percent one-tailed confidence interval with n-1 degrees of freedom (from appendix A of this subpart). (2) Other representations—(i) Rated hydraulic horsepower. The representative value of rated hydraulic horsepower of a basic model of dedicated-purpose pool pump must be the mean of the rated hydraulic horsepower for each tested unit. (ii) Dedicated-purpose pool pump motor total horsepower. The representative value of dedicated-purpose pool pump motor total horsepower of a basic model of dedicated-purpose pool pump must be the mean of the dedicated-purpose pool pump motor total horsepower for each tested unit. (iii) True power factor (PFi). The representative value of true power factor at each load point i of a basic model of dedicated-purpose pool pump must be the mean of the true power factors at that load point for each tested unit of dedicated-purpose pool pump. (b) Certification reports. (1) The requirements of §429.12 are applicable to pumps; and (2) Pursuant to §429.12(b)(13), a certification report must include the following public product-specific information: (i) For a pump subject to the test methods prescribed in section III of appendix A to subpart Y of part 431 of this chapter: PEICL; pump total head in feet (ft.) at BEP and nominal speed; volume per unit time (flow rate) in gallons per minute (gpm) at BEP and nominal speed; the nominal speed of rotation in revolutions per minute (rpm); calculated driver power input at each load point i (Pini), corrected to nominal speed, in horsepower (hp); full impeller diameter in inches (in.); and for RSV and ST pumps, the number of stages tested. (ii) For a pump subject to the test methods prescribed in section IV or V of appendix A to subpart Y of part 431 of this chapter: PEICL; pump total head in feet (ft.) at BEP and nominal speed; volume per unit time (flow rate) in gallons per minute (gpm) at BEP and nominal speed; the nominal speed of rotation in revolutions per minute (rpm); driver power input at each load point i (Pini), corrected to nominal speed, in horsepower (hp); full impeller diameter in inches (in.); whether the PEICL is calculated or tested; and for RSV and ST pumps, number of stages tested. (iii) For a pump subject to the test methods prescribed in section VI or VII of appendix A to subpart Y of part 431 of this chapter: PEIVL; pump total head in feet (ft.) at BEP and nominal speed; volume per unit time (flow rate) in gallons per minute (gpm) at BEP and nominal speed; the nominal speed of rotation in revolutions per minute (rpm); driver power input (measured as the input power to the driver and controls) at each load point i (Pini), corrected to nominal speed, in horsepower (hp); full impeller diameter in inches (in.); whether the PEIVL is calculated or tested; and for RSV and ST pumps, the number of stages tested. (iv) For a dedicated-purpose pool pump subject to the test methods prescribed in §431.464(b) of this chapter: weighted energy factor (WEF) in kilogallons per kilowatt-hour (kgal/kWh); rated hydraulic horsepower in horsepower (hp); the speed configuration for which the pump is being rated (i.e., single-speed, two-speed, multi-speed, or variable-speed); true power factor at all applicable test procedure load points i (dimensionless), as specified in Table 1 of appendix B or C to subpart Y of part 431 of this chapter, as applicable; dedicated-purpose pool pump nominal motor horsepower in horsepower (hp); dedicated-purpose pool pump motor total horsepower in horsepower (hp); dedicated-purpose pool pump service factor (dimensionless); for self-priming pool filter pumps, non-self-priming pool filter pumps, and waterfall pumps: The maximum head (in feet) which is based on the mean of the units in the tested sample; a statement regarding whether freeze protection is shipped enabled or disabled; for dedicated-purpose pool pumps distributed in commerce with freeze protection controls enabled: The default dry-bulb air temperature setting (in °F), default run time setting (in minutes), and default motor speed (in rpm); for self-priming pool filter pumps a statement regarding whether the pump is certified with NSF/ANSI 50-2015 (incorporated by reference, see §429.4) as self-priming; and, for self-priming pool filter pumps that are not certified with NSF/ANSI 50-2015 as self-priming: The vertical lift (in feet) and true priming time (in minutes) for the DPPP model. (v) For integral cartridge-filter and sand-filter pool pumps, the maximum run-time (in hours) of the pool pump control with which the integral cartridge-filter or sand-filter pump is distributed in commerce. (3) Pursuant to §429.12(b)(13), a certification report may include the following public product-specific information: (i) For a pump subject to the test methods prescribed in section III of appendix A to subpart Y of part 431 of this chapter: Pump efficiency at BEP in percent (%) and PERCL. (ii) For a pump subject to the test methods prescribed in section IV or V of appendix A to subpart Y of part 431 of this chapter: Pump efficiency at BEP in percent (%) and PERCL. (iii) For a pump subject to the test methods prescribed in section VI or VII of appendix A to subpart Y of part 431 of this chapter: Pump efficiency at BEP in percent (%) and PERVL. (iv) For a dedicated-purpose pool pump subject to the test methods prescribed in §431.464(b) of this chapter: Calculated driver power input and flow rate at each load point i (Pi and Qi), in horsepower (hp) and gallons per minute (gpm), respectively. (4) Pursuant to §429.12(b)(13), a certification report will include the following product-specific information: (i) For a pump subject to the test methods prescribed in section III of appendix A to subpart Y of part 431 of this chapter: The pump configuration (i.e., bare pump); and for ST pumps, the bowl diameter in inches (in.). (ii) For a pump subject to the test methods prescribed in section IV or V of appendix A to subpart Y of part 431 of this chapter: The pump configuration (i.e., pump sold with an electric motor); for pumps sold with electric motors regulated by DOE's energy conservation standards for electric motors at §431.25, the nominal motor efficiency in percent (%) and the motor horsepower (hp) for the motor with which the pump is being rated; and for ST pumps, the bowl diameter in inches (in.). (iii) For a pump subject to the test methods prescribed in section VI or VII of appendix A to subpart Y of part 431 of this chapter: The pump configuration (i.e., pump sold with a motor and continuous or non-continuous controls); for pumps sold with electric motors regulated by DOE's energy conservation standards for electric motors at §431.25, the nominal motor efficiency in percent (%) and the motor horsepower (hp) for the motor with which the pump is being rated; and for ST pumps, the bowl diameter in inches (in.). (c) Individual model numbers. (1) For a pump subject to the test methods prescribed in appendix A to subpart Y of part 431 of this chapter, each individual model number required to be reported pursuant to §429.12(b)(6) must consist of the following:
(2) Or must otherwise provide sufficient information to identify the specific driver model and/or controls model(s) with which a bare pump is distributed. [81 FR 4144, Jan. 25, 2016, as amended at 81 FR 4430, Jan. 26, 2016; 82 FR 36918, Aug. 7, 2017] |