Download the Code of Federal Regulations in XML.
The Electronic Code of Federal Regulations (e-CFR) is a regularly updated, unofficial editorial compilation of CFR material and Federal Register amendments produced by the National Archives and Records Administration's Office of the Federal Register (OFR) and the Government Publishing Office.
Parallel Table of Authorities and Rules for the Code of Federal Regulations and the United States Code
Text | PDF
Find, review, and submit comments on Federal rules that are open for comment and published in the Federal Register using Regulations.gov.
Purchase individual CFR titles from the U.S. Government Online Bookstore.
Find issues of the CFR (including issues prior to 1996) at a local Federal depository library.
Electronic Code of Federal Regulations
§52.01-135 Inspection and tests (modifies PG-90 through PG-100).
(a) Requirements. Inspection and test of boilers and boiler pressure parts shall be as indicated in PG-90 through PG-100 of section I of the ASME Boiler and Pressure Vessel Code (incorporated by reference; see 46 CFR 52.01-1) except as noted otherwise in this section.
(b) The inspections required by PG-90 through PG-100 of the ASME Code shall be performed by the “Authorized Inspector” as defined in PG-91 of section I of the ASME Boiler and Pressure Vessel Code (incorporated by reference; see 46 CFR 52.01-1). The Authorized Inspector shall hold a valid commission issued by the National Board of Boiler and Pressure Vessel Inspectors. After installation, boilers will be inspected for compliance with this part by the “Marine Inspector” as defined in §50.10-15 of this subchapter.
(c) Hydrostatic test (Modifies PG-99). Each new boiler shall be hydrostatically tested after installation to 11⁄2 times the maximum allowable working pressure as indicated in PG-99 of section I of the ASME Boiler and Pressure Vessel Code (incorporated by reference; see 46 CFR 52.01-1). Before the boilers are insulated, accessible parts of the boiler shall be emptied, opened up and all interior surfaces shall be examined by the marine inspector to ascertain that no defects have occurred due to the hydrostatic test.
(d) Operating tests. In addition to hydrostatic tests prescribed in paragraph (c) of this section, automatically controlled auxiliary boilers must be subjected to operating tests as specified in §§61.30-20, 61.35-1, 61.35-3, 62.30-10, 63.15-9, 63.25-3, and 63.25-5 of this chapter, as appropriate, or as directed by the Officer in Charge, Marine Inspection, for propulsion boilers, These tests are to be performed after final installation.
[CGFR 68-82, 33 FR 18815, Dec. 18, 1968, as amended by CGFR 69-127, 35 FR 9976, June 17, 1970; CGD 81-79, 50 FR 9433, Mar. 8, 1985; CGD 88-057, 55 FR 24236, June 15, 1990; USCG-2003-16630, 73 FR 65162, Oct. 31, 2008]