The Code of Federal Regulations (CFR) annual edition is the codification of the general and permanent rules published in the Federal Register by the departments and agencies of the Federal Government produced by the Office of the Federal Register (OFR) and the Government Publishing Office.
Download the Code of Federal Regulations in XML.
Parallel Table of Authorities and Rules for the Code of Federal Regulations and the United States Code
Text  PDF
Find, review, and submit comments on Federal rules that are open for comment and published in the Federal Register using Regulations.gov.
Purchase individual CFR titles from the U.S. Government Online Bookstore.
Find issues of the CFR (including issues prior to 1996) at a local Federal depository library.
[1]

Electronic Code of Federal Regulations
Title 10: Energy
Subpart B—CertificationContents §429.10 Purpose and scope. §429.11 General sampling requirements for selecting units to be tested. §429.12 General requirements applicable to certification reports. §429.13 Testing requirements. §429.14 Residential refrigerators, refrigeratorfreezers and freezers. §429.15 Room air conditioners. §429.16 Central air conditioners and heat pumps. §429.17 Residential water heaters. §429.18 Residential furnaces. §429.19 Dishwashers. §429.20 Residential clothes washers. §429.21 Residential clothes dryers. §429.22 Direct heating equipment. §429.23 Conventional cooking tops, conventional ovens, microwave ovens. §429.24 Pool heaters. §429.25 Television sets. §429.26 Fluorescent lamp ballasts. §429.27 General service fluorescent lamps, general service incandescent lamps, and incandescent reflector lamps. §429.28 Faucets. §429.29 Showerheads. §429.30 Water closets. §429.31 Urinals. §429.32 Ceiling fans. §429.33 Ceiling fan light kits. §429.34 Torchieres. §429.35 Bare or covered (no reflector) medium base compact fluorescent lamps. §429.36 Dehumidifiers. §429.37 Class A external power supplies. §429.38 Nonclass A external power supplies. [Reserved] §429.39 Battery chargers. §429.40 Candelabra base incandescent lamps and intermediate base incandescent lamps. §429.41 Commercial warm air furnaces. §429.42 Commercial refrigerators, freezers, and refrigeratorfreezers. §429.43 Commercial heating, ventilating, air conditioning (HVAC) equipment. §429.44 Commercial water heating equipment. §429.45 Automatic commercial ice makers. §429.46 Commercial clothes washers. §429.47 Distribution transformers. §429.48 Illuminated exit signs. §429.49 Traffic signal modules and pedestrian modules. §429.50 Commercial unit heaters. §429.51 Commercial prerinse spray valves. §429.52 Refrigerated bottled or canned beverage vending machines. §429.53 Walkin coolers and walkin freezers. §429.54 Metal halide lamp ballasts and fixtures. §429.58 Furnace fans. §429.60 Commercial packaged boilers. §429.70 Alternative methods for determining energy efficiency and energy use. §429.71 Maintenance of records. §429.72 Alternative methods for determining nonenergy ratings. Appendix A to Subpart B of Part 429—Student's tDistribution Values for Certification Testing §429.10 Purpose and scope.This subpart sets forth the procedures for manufacturers to certify that their covered products and covered equipment comply with the applicable energy conservation standards. §429.11 General sampling requirements for selecting units to be tested.(a) When testing of covered products or covered equipment is required to comply with section 323(c) of the Act, or to comply with rules prescribed under sections 324, 325, or 342, 344, 345 or 346 of the Act, a sample comprised of production units (or units representative of production units) of the basic model being tested shall be selected at random and tested, and shall meet the criteria found in §§429.14 through 429.54 of this subpart. Components of similar design may be substituted without additional testing if the substitution does not affect energy or water consumption. Any represented values of measures of energy efficiency, water efficiency, energy consumption, or water consumption for all individual models represented by a given basic model must be the same. (b) Unless otherwise specified, the minimum number of units tested shall be no less than two (except where a different minimum limit is specified in §§429.14 through 429.54 of this subpart); and §429.12 General requirements applicable to certification reports.(a) Certification. Each manufacturer, before distributing in commerce any basic model of a covered product or covered equipment subject to an applicable energy conservation standard set forth in parts 430 or 431, and annually thereafter on or before the dates provided in paragraph (d) of this section, shall submit a certification report to DOE certifying that each basic model meets the applicable energy conservation standard(s). The certification report(s) must be submitted to DOE in accordance with the submission procedures of paragraph (h) of this section. (b) Certification report. A certification report shall include a compliance statement (see paragraph (c) of this section), and for each basic model, the information listed in this paragraph (b). (1) Product or equipment type; (2) Product or equipment class (as denoted in the provisions of part 430 or 431 of this chapter containing the applicable energy conservation standard); (3) Manufacturer's name and address; (4) Private labeler's name(s) and address(es) (if applicable); (5) Brand name; (6) For each brand, the basic model number and the manufacturer's individual model number(s) in that basic model with the following exceptions: For external power supplies that are certified based on design families, the design family model number and the individual manufacturer's model numbers covered by that design family must be submitted for each brand. For walkin coolers, the basic model number for each brand must be submitted. For distribution transformers, the basic model number or kVA grouping model number (depending on the certification method) for each brand must be submitted. For commercial HVAC, WH, and refrigeration equipment, an individual manufacturer model number may be identified as a “private model number” if it meets the requirements of §429.7(b). (7) Whether the submission is for a new model, a discontinued model, a correction to a previously submitted model, data on a carryover model, or a model that has been found in violation of a voluntary industry certification program; (8) The test sample size (i.e., number of units tested for each basic model). Manufacturers must enter “0” if an AEDM was used in lieu of testing; (9) The certifying party's U.S. Customs and Border Protection (CBP) importer identification numbers assigned by CBP pursuant to 19 CFR 24.5, if applicable; (10) Whether certification is based upon any waiver of test procedure requirements under §430.27 or §431.401 of this chapter and the date(s) of such waiver(s); (11) Whether certification is based upon any exception relief from an applicable energy conservation standard and the date such relief was issued by DOE's Office of Hearings and Appeals; (12) If the test sample size is listed as “0” to indicate the certification is based upon the use of an alternate way of determining measures of energy conservation, identify the method used for determining measures of energy conservation (such as “AEDM,” “ARM,” or linear interpolation) and the approval date, if applicable, of any such alternate rating, testing, or efficiency determination method. Manufacturers of commercial packaged boilers, commercial water heating equipment, commercial refrigeration equipment and commercial HVAC equipment, must provide the manufacturer's designation (name or other identifier) of the AEDM used; and (13) Product specific information listed in §§429.14 through 429.58 of this chapter. (c) Compliance statement. The compliance statement required by paragraph (b) of this section shall include the date, the name of the company official signing the statement, and his or her signature, title, address, telephone number, and facsimile number and shall certify that: (1) The basic model(s) complies with the applicable energy conservation standard(s); (2) All required testing has been conducted in conformance with the applicable test requirements prescribed in parts 429, 430 and 431, as appropriate, or in accordance with the terms of an applicable test procedure waiver; (3) All information reported in the certification report is true, accurate, and complete; and (4) The manufacturer is aware of the penalties associated with violations of the Act, the regulations thereunder, and 18 U.S.C. 1001 which prohibits knowingly making false statements to the Federal Government. (d) Annual filing. All data required by paragraphs (a) through (c) shall be submitted to DOE annually, on or before the following dates:
(e) New model filing. (1) In addition to the annual filing schedule in paragraph (d) of this section, any new basic models must be certified pursuant to paragraph (a) of this section before distribution in commerce. A modification to a model that increases the model's energy or water consumption or decreases its efficiency resulting in rerating must be certified as a new basic model pursuant to paragraph (a) of this section. (2) For general service fluorescent lamps or incandescent reflector lamps: Prior to or concurrent with the distribution of a new basic model each manufacturer shall submit an initial certification report listing the basic model number, lamp wattage, and date of first manufacture (i.e., production date) for that basic model. The certification report must also state how the manufacturer determined that the lamp meets or exceeds the energy conservation standards, including a description of any testing or analysis the manufacturer performed. Manufacturers of general service fluorescent lamps and incandescent reflector lamps shall submit the certification report required by paragraph (b) of this section within one year after the first date of new model manufacture. (3) For distribution transformers, the manufacturer shall submit all information required in paragraphs (b) and (c) of this section for the new basic model, unless the manufacturer has previously submitted to the Department a certification report for a basic model of distribution transformer that is in the same kVA grouping as the new basic model. (f) Discontinued model filing. When production of a basic model has ceased and it is no longer being sold or offered for sale by the manufacturer or private labeler, the manufacturer shall report this discontinued status to DOE as part of the next annual certification report following such cessation. For each basic model, the report shall include the information specified in paragraphs (b)(1) through (b)(7) of this section. (g) Third party submitters. A manufacturer may elect to use a third party to submit the certification report to DOE (for example, a trade association, independent test lab, or other authorized representative, including a private labeler acting as a third party submitter on behalf of a manufacturer); however, the manufacturer is responsible for submission of the certification report to DOE. DOE may refuse to accept certification reports from third party submitters who have failed to submit reports in accordance with the rules of this part. The third party submitter must complete the compliance statement as part of the certification report. Each manufacturer using a third party submitter must have an authorization form on file with DOE. The authorization form includes a compliance statement, specifies the third party authorized to submit certification reports on the manufacturer's behalf and provides the contact information and signature of a company official. (h) Method of submission. Reports required by this section must be submitted to DOE electronically at http://www.regulations.doe.gov/ccms (CCMS). A manufacturer or third party submitter can find productspecific templates for each covered product or covered equipment with certification requirements online at https://www.regulations.doe.gov/ccms/templates.html. Manufacturers and third party submitters must submit a registration form, signed by an officer of the company, in order to obtain access to CCMS. (i) Compliance dates. For any product subject to an applicable energy conservation standard for which the compliance date has not yet occurred, a certification report must be submitted not later than the compliance date for the applicable energy conservation standard. The covered products enumerated below are subject to the stated compliance dates for initial certification: (1) Commercial warm air furnaces, packaged terminal air conditioners, and packaged terminal heat pumps, July 1, 2014; (2) Commercial gasfired and oilfired instantaneous water heaters less than 10 gallons and commercial gasfired and oilfired hot water supply boilers less than 10 gallons, October 1, 2014; (3) All other types of covered commercial water heaters except those specified in paragraph (i)(2) of this section, commercial packaged boilers with input capacities less than or equal to 2.5 million Btu/h, and selfcontained commercial refrigeration equipment with solid or transparent doors, December 31, 2014; (4) Variable refrigerant flow air conditioners and heat pumps, March 31, 2015; (5) Small, large, or very large aircooled, watercooled, evaporativelycooled, and watersource commercial air conditioning and heating equipment, single package vertical units, computer room air conditioners, commercial packaged boilers with input capacities greater than 2.5 million Btu/h, and all other types of commercial refrigeration equipment except those specified in paragraph (i)(3) of this section, July 1, 2015. [76 FR 12451, Mar. 7, 2011; 76 FR 24762, May 2, 2011, as amended at 76 FR 38292, June 30, 2011; 76 FR 65365, Oct. 21, 2011; 77 FR 76830, Dec. 31, 2012; 78 FR 79593, Dec. 31, 2013; 79 FR 25500, May 5, 2014; 79 FR 38208, July 3, 2014] §429.13 Testing requirements.(a) The determination that a basic model complies with an applicable energy conservation standard shall be determined from the values derived pursuant to the applicable testing and sampling requirements set forth in parts 429, 430 and 431. The determination that a basic model complies with the applicable design standard shall be based upon the incorporation of specific design requirements in parts 430 and 431 or as specified in section 325 and 342 of the Act. (b) Where DOE has determined a particular entity is in noncompliance with an applicable standard or certification requirement, DOE may impose additional testing requirements as a remedial measure. §429.14 Residential refrigerators, refrigeratorfreezers and freezers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to residential refrigerators, refrigeratorfreezers and freezers; and (2) For each basic model of residential refrigerators, refrigeratorfreezers, and freezers, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of estimated annual operating cost, energy consumption, or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and (ii) Any represented value of the energy factor or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
(3) The value of total refrigerated volume of a basic model reported in accordance with paragraph (b)(2) of this section shall be the mean of the total refrigerated volumes measured for each tested unit of the basic model or the total refrigerated volume of the basic model as calculated in accordance with §429.72(c). (b) Certification reports. (1) The requirements of §429.12 are applicable to residential refrigerators, refrigeratorfreezers and freezers; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The annual energy use in kilowatt hours per year (kWh/yr); the total refrigerated volume in cubic feet (ft3); and the adjusted total volume in cubic feet (ft3). (3) Pursuant to §429.12(b)(13), a certification report shall include the following additional productspecific information: whether the basic model has variable defrost control (in which case, manufacturers must also report the values, if any, of CTL and CTM (For an example, see section 5.2.1.3 in appendix A to subpart B of 10 CFR part 430) used in the calculation of energy consumption), whether the basic model has variable antisweat heater control (in which case, manufacturers must also report the values of heater Watts at the ten humidity levels (5%, 15%, 25%, 35%, 45%, 55%, 65%, 75%, 85%, and 95%) used to calculate the variable antisweat heater “Correction Factor”), and whether testing has been conducted with modifications to the standard temperature sensor locations specified by the figures referenced in section 5.1 of appendices A1, B1, A, and B to subpart B of 10 CFR part 430. [76 FR 12451, Mar. 7, 2011; 76 FR 24762, May 2, 2011, as amended at 79 FR 22348, Apr. 21, 2014] §429.15 Room air conditioners.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to room air conditioners; and (2) For each basic model of room air conditioners, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of estimated annual operating cost, energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
or, (B) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (ii) Any represented value of the energy efficiency ratio or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
or, (B) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to room air conditioners; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), cooling capacity in British thermal units per hour (Btu/h), and the electrical power input in watts (W). [76 FR 12451, Mar. 7, 2011; 76 FR 24763, May 2, 2011] §429.16 Central air conditioners and heat pumps.(a) Sampling plan for selection of units for testing. (1) The general requirements of §429.11 are applicable to central air conditioners and heat pumps; and (2)(i) For central air conditioners and heat pumps, each singlepackage system and each condensing unit (outdoor unit) of a splitsystem, when combined with a selected evaporator coil (indoor unit) or a set of selected indoor units, must have a sample of sufficient size tested in accordance with the applicable provisions of this subpart. The represented values for any model of a singlepackage system, any model of a tested splitsystem combination, any model of a tested minisplit system combination, or any model of a tested multisplit system combination must be assigned such that— (A) Any represented value of annual operating cost, energy consumption or other measure of energy consumption of the central air conditioner or heat pump for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
Or, (2) The upper 90 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (B) Any represented value of the energy efficiency or other measure of energy consumption of the central air conditioner or heat pump for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
Or, (2) The lower 90 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(C) For heat pumps, all units of the sample population must be tested in both the cooling and heating modes and the results used for determining the heat pump's certified Seasonal Energy Efficiency Ratio (SEER) and Heating Seasonal Performance Factor (HSPF) ratings in accordance with paragraph (a)(2)(i)(B) of this section. (ii) For splitsystem air conditioners and heat pumps, the condenserevaporator coil combination selected for tests pursuant to paragraph (a)(2)(i) of this section shall include the evaporator coil that is likely to have the largest volume of retail sales with the particular model of condensing unit. For minisplit condensing units that are designed to always be installed with more than one indoor unit, a “tested combination” as defined in 10 CFR 430.2 shall be used for tests pursuant to paragraph (a)(2)(i) of this section. For multisplit systems, each model of condensing unit shall be tested with two different sets of indoor units. For one set, a “tested combination” composed entirely of nonducted indoor units shall be used. For the second set, a “tested combination” composed entirely of ducted indoor units shall be used. However, for any splitsystem air conditioner having a singlespeed compressor, the condenserevaporator coil combination selected for tests pursuant to paragraph (a)(2)(i) of this section shall include the indoor coilonly unit that is likely to have the largest volume of retail sales with the particular model of outdoor unit. This coilonly requirement does not apply to splitsystem air conditioners that are only sold and installed with blowercoil indoor units, specifically minisplits, multisplits, and throughthewall units. This coilonly requirement does not apply to any splitsystem heat pumps. For every other splitsystem combination that includes the same model of condensing unit but a different model of evaporator coil and for every other minisplit and multisplit system that includes the same model of condensing unit but a different set of evaporator coils, whether the evaporator coil(s) is manufactured by the same manufacturer or by a component manufacturer, either— (A) A sample of sufficient size, comprised of production units or representing production units, must be tested as complete systems with the resulting ratings for the outdoor unitindoor unit(s) combination obtained in accordance with paragraphs (a)(2)(i)(A) and (a)(2)(i)(B) of this section; or (B) The representative values of the measures of energy efficiency must be assigned as follows: (1) Using an alternative rating method (ARM) that has been approved by DOE in accordance with the provisions of §429.70(e)(1) and (2); or (2) For multisplit systems composed entirely of nonducted indoor units, set equal to the system tested in accordance with paragraph (a)(2)(i) of this section whose tested combination was entirely nonducted indoor units; or (3) For multisplit systems composed entirely of ducted indoor units, set equal to the system tested in accordance with paragraph (a)(2)(i) of this section when the tested combination was entirely ducted indoor units; or (4) For multisplit systems having a mix of nonducted and ducted indoor units, set equal to the mean of the values for the two systems—one having the tested combination of all nonducted units and the second having the tested combination of all ducted indoor units—tested in accordance with paragraph (a)(2)(i) of this section. (iii) Whenever the representative values of the measures of energy consumption, as determined by the provisions of paragraph (a)(2)(ii)(B) of this section, do not agree within 5 percent of the energy consumption as determined by actual testing, the values determined by actual testing must be used to comply with section 323(c) of the Act or to comply with rules under section 324 of the Act. (b) Certification reports. (1) The requirements of §429.12 are applicable to central air conditioners and heat pumps; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) Residential central air conditioners: The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)), the cooling capacity in British thermal units per hour (Btu/h), and the manufacturer and individual manufacturer's model numbers of the indoor and outdoor unit. For central air conditioners whose seasonal energy efficiency ratio is based on an installation that includes a particular model of ducted air mover (e.g., furnace, air handler, blower kit), the manufacturer's model number of this ducted air mover must be included among the model numbers listed on the certification report. (ii) Residential central air conditioning heat pumps: The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)), the cooling capacity in British thermal units per hour (Btu/h), the heating seasonal performance factor (HSPF in British thermal units per Watthour (Btu/Wh)), and the manufacturer and individual model numbers of the indoor and outdoor unit. For central air conditioning heat pumps whose seasonal energy efficiency ratio and heating seasonal performance factor are based on an installation that includes a particular model of ducted air mover (e.g., furnace, air handler, blower kit), the model number of this ducted air mover must be included among the model numbers listed on the certification report. (iii) Small duct, high velocity air conditioners: The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)) and the cooling capacity in British thermal units per hour (Btu/h). (iv) Small duct, high velocity heat pumps: The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)), the heating seasonal performance factor (HSPF in British thermal units per Watthour (Btu/Wh)), and the cooling capacity in British thermal units per hour (Btu/h). (iv) Space constrained air conditioners: The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)) and the cooling capacity in British thermal units per hour (Btu/h). (v) Space constrained heat pumps: The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)), the coefficient of performance, and the cooling capacity in British thermal units per hour (Btu/h). (c) Alternative methods for determining efficiency or energy use for central air conditioners and heat pumps can be found in §429.70 of this subpart. [76 FR 12451, Mar. 7, 2011; 76 FR 24763, May 2, 2011] §429.17 Residential water heaters.Link to an amendment published at 79 FR 40565, July 11, 2014. (a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to residential water heaters; and (2) For each basic model of residential water heaters, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of estimated annual operating cost, energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and (ii) Any represented value of the energy factor or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to residential water heaters; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The energy factor (EF), rated storage volume in gallons (gal), first hour rating (maximum gallons per minute), and recovery efficiency (percent). [76 FR 12451, Mar. 7, 2011; 76 FR 24764, May 2, 2011] §429.18 Residential furnaces.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to residential furnaces; and (2) (i) For each basic model of furnaces, other than basic models of those sectional castiron boilers (which may be aggregated into groups having identical intermediate sections and combustion chambers) a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of estimated annual operating cost, energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
Or, (2) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (B) Any represented value of the annual fuel utilization efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
Or, (2) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(ii) For the lowest capacity basic model of a group of basic models of those sectional castiron boilers having identical intermediate sections and combustion chambers, a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of estimated annual operating cost, energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
Or, (2) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (B) Any represented value of the fuel utilization efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
Or, (2) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(iii) For the highest capacity basic model of a group of basic models of those sectional castiron boilers having identical intermediate sections and combustion chambers, a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of estimated annual operating cost, energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
Or, (2) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (B) Any represented value of the fuel utilization efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
Or, (2) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(iv) For each basic model or capacity other than the highest or lowest of the group of basic models of sectional castiron boilers having identical intermediate sections and combustion chambers, represented values of measures of energy consumption shall be determined by either— (A) A linear interpolation of data obtained for the smallest and largest capacity units of the family, or (B) Testing a sample of sufficient size to ensure that: (1) Any represented value of estimated annual operating cost, energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (i) The mean of the sample, where:
Or, (ii) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (2) Any represented value of the energy factor or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (i) The mean of the sample, where:
Or, (ii) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(v) Whenever measures of energy consumption determined by linear interpolation do not agree with measures of energy consumption determined by actual testing, the values determined by testing must be used for certification. (vi) In calculating the measures of energy consumption for each unit tested, use the design heating requirement corresponding to the mean of the capacities of the units of the sample. (b) Certification reports. (1) The requirements of §429.12 are applicable to residential furnaces; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) Residential furnaces and boilers: The annual fuel utilization efficiency (AFUE) in percent (%) and the input capacity in British thermal units per hour (Btu/h). (ii) For castiron sectional boilers: The type of ignition system for gasfired steam and hot water boilers. (3) Pursuant to §429.12(b)(13), a certification report shall include the following additional productspecific information: For castiron sectional boilers: a declaration of whether certification is based on linear interpolation or testing. For hot water boilers, a declaration that the manufacturer has incorporated the applicable design requirements. [76 FR 12451, Mar. 7, 2011; 76 FR 24765, May 2, 2011, as amended at 76 FR 38292, June 30, 2011] §429.19 Dishwashers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to dishwashers; and (2) For each basic model of dishwashers, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of estimated annual operating cost, energy or water consumption or other measure of energy or water consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (ii) Any represented value of the energy or water factor or other measure of energy or water consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to dishwashers; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The estimated annual energy use in kilowatt hours per year (kWh/yr) and the water consumption in gallons per cycle. (3) Pursuant to §429.12(b)(13), a certification report shall include the following additional productspecific information when using appendix C or appendix C1: the capacity in number of place settings as specified in ANSI/AHAM DW11992 when using appendix C (incorporated by reference, see §429.4) and ANSI/AHAM DW12010 when using appendix C1 (incorporated by reference, see §429.4), presence of a soil sensor (if yes, the number of cycles required to reach calibration), and the water inlet temperature used for testing in degrees Fahrenheit ( °F). When using appendix C1, additionally: the cycle selected for energy testing and whether that cycle is soilsensing, the options selected for the energy test, and presence of a builtin water softening system (if yes, the energy use in kilowatthours and the water use in gallons required for each regeneration of the water softening system, the number of regeneration cycles per year, and data and calculations used to derive these values). [76 FR 12451, Mar. 7, 2011; 76 FR 24766, May 2, 2011, as amended at 77 FR 31962, May 30, 2012; 77 FR 65977, Oct. 31, 2012] §429.20 Residential clothes washers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to residential clothes washers; and (2) For each basic model of residential clothes washers, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of the water factor, integrated water factor, the estimated annual operating cost, the energy or water consumption, or other measure of energy or water consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (ii) Any represented value of the modified energy factor, integrated modified energy factor, or other measure of energy or water consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to residential clothes washers; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) For residential clothes washers manufactured before March 7, 2015: The modified energy factor (MEF) in cubic feet per kilowatt hour per cycle (cu ft/kWh/cycle) and the capacity in cubic feet (cu ft). For standardsize residential clothes washers, a water factor (WF) in gallons per cycle per cubic feet (gal/cycle/cu ft). (ii) For residential clothes washers manufactured on or after March 7, 2015: The integrated modified energy factor (IMEF) in cu ft/kWh/cycle, the integrated water factor (IWF) in gal/cycle/cu ft, the capacity in cu ft and the type of loading (toploading or frontloading). (3) Pursuant to §429.12(b)(13), a certification report shall include the following additional productspecific information: When using appendix J2, a list of all cycle selections comprising the complete energy test cycle for each basic model. [76 FR 12451, Mar. 7, 2011; 76 FR 24767, May 2, 2011, as amended at 77 FR 13936, Mar. 7, 2012; 77 FR 32379, May 31, 2012] §429.21 Residential clothes dryers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to clothes dryers; and (2) For each basic model of clothes dryers a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of estimated annual operating cost, energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (ii) Any represented value of the energy factor, combined energy factor, or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(3) The capacity of a basic model reported in accordance with paragraph (b)(2) of this section shall be the mean of the capacities measured for each tested unit of the basic model. (b) Certification reports. (1) The requirements of §429.12 are applicable to clothes dryers; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: When using appendix D, the energy factor in pounds per kilowatt hours (lb/kWh), the capacity in cubic feet (cu ft), the voltage in volts (V) (for electric dryers only), an indication if the dryer has automatic termination controls, and the hourly British thermal unit (Btu) rating of the burner (for gas dryers only); when using appendix D1, the combined energy factor in pounds per kilowatt hours (lb/kWh), the capacity in cubic feet (cu ft), the voltage in volts (V) (for electric dryers only), an indication if the dryer has automatic termination controls, and the hourly Btu rating of the burner (for gas dryers only); when using appendix D2, the combined energy factor in pounds per kilowatt hours (lb/kWh), the capacity in cubic feet (cu ft), the voltage in volts (V) (for electric dryers only), an indication if the dryer has automatic termination controls, the hourly Btu rating of the burner (for gas dryers only), and a list of the cycle setting selections for the energy test cycle as recorded in section 3.4.7 of appendix D2 to Subpart B of Part 430. [76 FR 12451, Mar. 7, 2011; 76 FR 24767, May 2, 2011, as amended at 78 FR 49644, Aug. 14, 2013] §429.22 Direct heating equipment.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to direct heating equipment; and (2) (i) For each basic model of direct heating equipment (not including furnaces) a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of estimated annual operating cost, energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
Or, (2) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (B) Any represented value of the fuel utilization efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
Or, (2) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(ii) In calculating the measures of energy consumption for each unit tested, use the design heating requirement corresponding to the mean of the capacities of the units of the sample. (b) Certification reports. (1) The requirements of §429.12 are applicable to direct heating equipment; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: Direct heating equipment, the annual fuel utilization efficiency (AFUE) in percent (%), the mean input capacity in British thermal units per hour (Btu/h), and the mean output capacity in British thermal units per hour (Btu/h). [76 FR 12451, Mar. 7, 2011; 76 FR 24768, May 2, 2011, as amended at 76 FR 38292, June 30, 2011] §429.23 Conventional cooking tops, conventional ovens, microwave ovens.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to conventional cooking tops, conventional ovens and microwave ovens; and (2) For each basic model of conventional cooking tops, conventional ovens and microwave ovens a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of estimated annual operating cost, energy consumption, standby mode power consumption, off mode power consumption, or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (ii) Any represented value of the energy factor, integrated energy factor, or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to conventional cooking tops, conventional ovens and microwave ovens; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: For conventional cooking tops and conventional ovens: the type of pilot light and a declaration that the manufacturer has incorporated the applicable design requirements. For microwave ovens, the average standby power in watts. [76 FR 12451, Mar. 7, 2011; 76 FR 24769, May 2, 2011, as amended at 77 FR 65977, Oct. 31, 2012; 78 FR 4025, Jan. 18, 2013; 78 FR 36368, June 17, 2013] §429.24 Pool heaters.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to pool heaters; and (2) For each basic model of pool heater a sample of sufficient size shall be randomly selected and tested to ensure that any represented value of the thermal efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of:
(i) The mean of the sample, where: Or, (ii) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to pool heaters; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The thermal efficiency in percent (%) and the input capacity in British thermal units per hour (Btu/h). [76 FR 12451, Mar. 7, 2011; 76 FR 24769, May 2, 2011] §429.25 Television sets.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to televisions; and (2) For each basic model of television, samples shall be randomly selected and tested to ensure that— (i) Any represented value of power consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
and x̅ is the sample mean; n is the number of samples; and xi is the ith sample; Or, (B) For on mode power consumption, the upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the tstatistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from appendix A of this subpart). And (C) For standby mode power consumption and power consumption measurements in modes other than on mode, the upper 90 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.90 is the tstatistic for a 90% onetailed confidence interval with n−1 degrees of freedom (from appendix A of this subpart). (ii) Any represented annual energy consumption of a basic model shall be determined by applying the AEC calculation in section 8.2 of Appendix H to subpart B of 10 CFR Part 430 to the represented values of power consumption as calculated pursuant to paragraph (a)(2)(i) of this section. (iii) Rounding requirements. The represented value of power consumption and the represented annual energy consumption shall be rounded as follows: (A) For power consumption in the on, standby, and off modes, the represented value shall be rounded according to the accuracy requirements specified in section 3.3.3 of Appendix H to subpart B of 10 CFR Part 430. (B) For annual energy consumption, the represented value shall be rounded according to the rounding requirements specified in section 8.3 of Appendix H to subpart B of 10 CFR Part 430. (b) [Reserved] [78 FR 63840, Oct. 25, 2013] §429.26 Fluorescent lamp ballasts.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to fluorescent lamp ballasts; and (2) For each basic model of fluorescent lamp ballasts, a sample of sufficient size, not less than four, shall be randomly selected and tested to ensure that— (i) Any represented value of estimated annual energy operating costs, energy consumption, or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 99 percent confidence limit (UCL) of the true mean divided by 1.01, where:
and (ii) Any represented value of the ballast efficacy factor or other measure of the energy consumption of a basic model for which consumers would favor a higher value shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 99 percent confidence limit (LCL) of the true mean divided by 0.99, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to fluorescent lamp ballasts; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The ballast efficacy factor, the ballast power factor, the number of lamps operated by the ballast, and the type of lamps operated by the ballast. [76 FR 12451, Mar. 7, 2011; 76 FR 24769, May 2, 2011] §429.27 General service fluorescent lamps, general service incandescent lamps, and incandescent reflector lamps.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to general service fluorescent lamps, general service incandescent lamps and incandescent reflector lamps; and (2)(i) For each basic model of general service fluorescent lamp and incandescent reflector lamp, samples of production lamps shall be obtained from a 12month period, tested, and the results averaged. A minimum sample of 21 lamps shall be tested. The manufacturer shall randomly select a minimum of three lamps from each month of production for a minimum of 7 out of the 12month period. In the instance where production occurs during fewer than 7 of such 12 months, the manufacturer shall randomly select 3 or more lamps from each month of production, where the number of lamps selected for each month shall be distributed as evenly as practicable among the months of production to attain a minimum sample of 21 lamps. Any represented value of lamp efficacy of a basic model shall be based on the sample and shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by .97, where:
(ii) For each basic model of general service fluorescent lamp and general service incandescent lamp, the color rendering index (CRI) shall be measured from the same lamps selected for the lumen output and watts input measurements in paragraphs (a)(2)(i) and (a)(2)(iii) of this section, i.e., the manufacturer shall measure all lamps for lumens, watts input, and CRI. The CRI shall be represented as the average of a minimum sample of 21 lamps and shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by .97, where:
(iii) For each basic model of general service incandescent lamp, for measurements of rated wattage and rated lumen output, samples of production lamps shall be obtained from a 12month period, tested, and the results averaged. A minimum sample of 21 lamps shall be tested. The manufacturer shall randomly select a minimum of three lamps from each month of production for a minimum of 7 out of the 12month period. In the instance where production occurs during fewer than 7 of such 12 months, the manufacturer shall randomly select 3 or more lamps from each month of production, where the number of lamps selected for each month shall be distributed as evenly as practicable among the months of production to attain a minimum sample of 21 lamps. Any represented value of rated wattage of a basic model shall be based on the sample and shall be greater than or equal to the higher of: (A) The mean of the sample, where:
and, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.03, where:
and x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% twotailed confidence interval with n1 degrees of freedom (from Appendix A to this subpart). (iv) For each basic model of general service incandescent lamp, for measurements of rated lifetime, a minimum sample of 21 lamps shall be tested. The manufacturer shall randomly select a minimum of three lamps from each month of production for a minimum of 7 out of the 12month period. In the instance where production occurs during fewer than 7 of such 12 months, the manufacturer shall randomly select three or more lamps from each month of production, where the number of lamps selected for each month shall be distributed as evenly as practicable among the months of production to attain a minimum sample of 21 lamps. The lifetime shall be represented as the length of operating time between first use and failure of 50 percent of the sample size, in accordance with test procedures described in section 4.2 of Appendix R to subpart B of part 430 of this chapter. Compliance will be determined by the percentage of sample size that meets the minimum rated lifetime. (b) Certification reports. (1) The requirements of §429.12 are applicable to general service fluorescent lamps, general service incandescent lamps and incandescent reflector lamps; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) General service fluorescent lamps: the testing laboratory's National Voluntary Laboratory Accreditation Program (NVLAP) identification number or other NVLAPapproved accreditation identification, production dates of the units tested, the 12month average lamp efficacy in lumens per watt (lm/W), lamp wattage (W), correlated color temperature in Kelvin (K), and the 12month average Color Rendering Index (CRI). (ii) Incandescent reflector lamps: The laboratory's NVLAP identification number or other NVLAPapproved accreditation identification, production dates of the units tested, the 12month average lamp efficacy in lumens per watt (lm/W), and lamp wattage (W). (iii) General service incandescent lamps: The testing laboratory's National Voluntary Laboratory Accreditation Program (NVLAP) identification number or other NVLAPapproved accreditation identification, production dates of the units tested, the 12month average maximum rate wattage in watts (W), the 12month average minimum rated lifetime (hours), and the 12month average Color Rendering Index (CRI). (c) Test data. Manufacturers must include the production date codes and the accompanying decoding scheme corresponding to all of the units tested for a given basic model in the detailed test records maintained under §429.71. [76 FR 12451, Mar. 7, 2011; 76 FR 24770, May 2, 2011, as amended at 76 FR 38292, June 30, 2011; 77 FR 4215, Jan. 27, 2012] §429.28 Faucets.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to faucets; and (2) For each basic model of faucet, a sample of sufficient size shall be randomly selected and tested to ensure that any represented value of water consumption of a basic model for which consumers favor lower values shall be no less than the higher of the higher of: (i) The mean of the sample, where:
Or, (ii) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to faucets; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: For nonmetering faucets, the maximum water use in gallons per minute (gpm) rounded to the nearest 0.1 gallon; for metering faucets, the maximum water use in gallons per cycle (gal/cycle) rounded to the nearest 0.01 gallon; and for all faucet types, the flow water pressure in pounds per square inch (psi). [76 FR 12451, Mar. 7, 2011; 76 FR 24771, May 2, 2011, as amended at 78 FR 62985, Oct. 23, 2013] §429.29 Showerheads.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to showerheads; and (2) For each basic model of a showerhead, a sample of sufficient size shall be randomly selected and tested to ensure that any represented value of water consumption of a basic model for which consumers favor lower values shall be greater than or equal to the higher of: (i) The mean of the sample, where:
Or, (ii) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to showerheads; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The maximum water use in gallons per minute (gpm) rounded to the nearest 0.1 gallon, the maximum flow water pressure in pounds per square inch (psi), and a declaration that the showerhead meets the requirements of §430.32(p) pertaining to mechanical retention of the flowrestricting insert, if applicable. [76 FR 12451, Mar. 7, 2011; 76 FR 24771, May 2, 2011, as amended at 78 FR 62985, Oct. 23, 2013] §429.30 Water closets.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to water closets; and (2) For each basic model of water closet, a sample of sufficient size shall be randomly selected and tested to ensure that any represented value of water consumption of a basic model for which consumers favor lower values shall be greater than or equal to the higher of: (i) The mean of the sample, where:
Or, (ii) The upper 90 percent confidence limit (UCL) of the true mean divided by 1.1, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to water closets; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The maximum water use in gallons per flush (gpf), rounded to the nearest 0.01 gallon. For dualflush water closets, the maximum water use to be reported is the flush volume observed when tested in the fullflush mode. [76 FR 12451, Mar. 7, 2011; 76 FR 24771, May 2, 2011, as amended at 78 FR 62986, Oct. 23, 2013] §429.31 Urinals.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to urinals; and (2) For each basic model of urinal, a sample of sufficient size shall be randomly selected and tested to ensure that any represented value of water consumption of a basic model for which consumers favor lower values shall be greater than or equal to the higher of: (i) The mean of the sample, where:
Or, (ii) The upper 90 percent confidence limit (UCL) of the true mean divided by 1.1, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to urinals; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The maximum water use in gallons per flush (gpf), rounded to the nearest 0.01 gallon, and for troughtype urinals, the maximum flow rate in gallons per minute (gpm), rounded to the nearest 0.01 gallon, and the length of the trough in inches (in). [76 FR 12451, Mar. 7, 2011; 76 FR 24771, May 2, 2011, as amended at 78 FR 62986, Oct. 23, 2013] §429.32 Ceiling fans.(a) Sampling plan for selection of units for testing. The requirements of §429.11 are applicable to ceiling fans. (b) Certification reports. (1) The requirements of §429.12 are applicable to ceiling fans; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The number of speeds within the ceiling fan controls and a declaration that the manufacturer has incorporated the applicable design requirements. §429.33 Ceiling fan light kits.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to ceiling fan light kits; and (2) For each basic model of ceiling fan light kit with sockets for medium screw base lamps or pinbased fluorescent lamps selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any value of estimated energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.1, where:
and (ii) Any represented value of the efficacy or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.9, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to ceiling fan light kits; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) Ceiling fan light kits with sockets for medium screw base lamps: the rated wattage in watts (W) and the system's efficacy in lumens per watt (lm/W). (ii) Ceiling fan light kits with pinbased sockets for fluorescent lamps: the rated wattage in watts (W), the system's efficacy in lumens per watt (lm/W), and the length of the lamp in inches (in). (iii) Ceiling fan light kits with any other socket type: the rated wattage in watts (W) and the number of individual sockets. (3) Pursuant to §429.12(b)(13), a certification report shall include the following additional productspecific information: Ceiling fan light kits with any other socket type: a declaration that the basic model meets the applicable design requirement and the features that have been incorporated into the ceiling fan light kit to meet the applicable design requirement (e.g., circuit breaker, fuse, ballast). [76 FR 12451, Mar. 7, 2011; 76 FR 24772, May 2, 2011] §429.34 Torchieres.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to torchieres; and (2) Reserved (b) Certification reports. (1) The requirements of §429.12 are applicable to torchieres; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following additional productspecific information: A declaration that the basic model meets the applicable design requirement and the features that have been incorporated into the torchiere to meet the applicable design requirement (e.g., circuit breaker, fuse, ballast). §429.35 Bare or covered (no reflector) medium base compact fluorescent lamps.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to bare or covered (no reflector) medium base compact fluorescent lamps; and (2) For each basic model of bare or covered (no reflector) medium base compact fluorescent lamp (i) No less than five units per basic model must be used when testing for the efficacy, 1,000hour lumen maintenance, and the lumen maintenance. Each unit must be tested in the baseup position unless the product is labeled restricted by the manufacturer, in which case the unit should be tested in the manufacturer specified position. Any represented value of efficacy, 1,000hour lumen maintenance, and lumen maintenance shall be based on a sample randomly selected and tested to ensure that the represented value is less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 97.5 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(ii) No less than 6 unique units (i.e., units that have not previously been tested) per basic model must be used when testing for the rapid cycle stress. Each unit can be tested in the base up or base down position as stated by the manufacturer. (iii) No less than 10 units per basic model must be used when testing for the average rated lamp life. Half the sample should be tested in the base up position and half of the sample should be tested in the base down position, unless specific use or position appears on the packaging of that particular unit. (b) Certification reports. (1) The requirements of §429.12 are applicable to bare or covered medium base compact fluorescent lamps; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The testing laboratory's NVLAP identification number or other NVLAPapproved accreditation identification, the minimum initial efficacy in lumens per watt (lm/W), the lumen maintenance at 1,000 hours in percent (%), the lumen maintenance at 40 percent of rated life in percent (%), the rapid cycle stress test in number of units passed, and the lamp life in hours (h). [76 FR 12451, Mar. 7, 2011; 76 FR 24772, May 2, 2011, as amended at 76 FR 38292, June 30, 2011] §429.36 Dehumidifiers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to dehumidifiers; and (2) For each basic model of dehumidifier selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and (ii) Any represented value of the energy factor, integrated energy factor, or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to dehumidifiers; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The energy factor in liters per kilowatt hour (liters/kWh) and capacity in pints per day. [76 FR 12451, Mar. 7, 2011; 76 FR 24773, May 2, 2011, as amended at 77 FR 65977, Oct. 31, 2012] §429.37 Class A external power supplies.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to external power supplies; and (2) For each basic model of external power supply selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of the estimated energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 97.5 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (ii) Any represented value of the estimated energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 97.5 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to external power supplies except that required information may be reported on the basis of a basic model or a design family. If certifying using a design family, for §429.12(b)(6), report the individual manufacturer's model numbers covered by the design family. (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) External power supplies: The average active mode efficiency as a percent (%), noload mode power consumption in watts (W), nameplate output power in watts (W), and, if missing from the nameplate, the output current in amperes (A) of the basic model or the output current in amperes (A) of the highest and lowestvoltage models within the external power supply design family. (ii) Switchselectable singlevoltage external power supplies: The average active mode efficiency as a percent (%), noload mode power consumption in watts (W) at the lowest and highest selectable output voltage, nameplate output power in watts (W), and, if missing from the nameplate, the output current in amperes (A). (iii) External power supplies that are exempt from noload mode requirements under §430.32(w)(1)(iii): A statement that the product is designed to be connected to a security or life safety alarm or surveillance system component, the average active mode efficiency as a percent (%), the nameplate output power in watts (W), and if missing from the nameplate, the certification report must also include the output current in amperes (A) of the basic model or the output current in amperes (A) of the highest and lowestvoltage models within the external power supply design family. [76 FR 12451, Mar. 7, 2011; 76 FR 24773, May 2, 2011, as amended at 76 FR 57899, Sept. 19, 2011] §429.38 Nonclass A external power supplies. [Reserved]§429.39 Battery chargers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to battery chargers; and (2) For each basic model of battery charger selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of the estimated nonactive energy ratio or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 97.5 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (ii) Any represented value of the estimated nonactive energy ratio or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 97.5 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. [Reserved] [76 FR 12451, Mar. 7, 2011; 76 FR 24774, May 2, 2011] §429.40 Candelabra base incandescent lamps and intermediate base incandescent lamps.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to candelabra base incandescent lamps; and (2) For each basic model of candelabra base incandescent lamp and intermediate base incandescent lamp, a minimum sample of 21 lamps shall be randomly selected and tested. Any represented value of lamp wattage of a basic model shall be based on the sample and shall be less than or equal to the lower of: (i) The mean of the sample, where:
Or, (ii) The lower 97.5 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to candelabra base and intermediate base incandescent lamps; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) Candelabra base incandescent lamp: The rated wattage in watts (W). (ii) Intermediate base incandescent lamp: The rated wattage in watts (W). [76 FR 12451, Mar. 7, 2011; 76 FR 24774, May 2, 2011] §429.41 Commercial warm air furnaces.(a) Determination of represented value. Manufacturers must determine the represented value, which includes the certified rating, for each basic model of commercial warm air furnace either by testing, in conjunction with the applicable sampling provisions, or by applying an AEDM. (1) Units to be tested. (i) If the represented value is determined through testing, the general requirements of §429.11 are applicable; and (ii) For each basic model selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
and, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; Or, (2) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from Appendix A to subpart B of part 429). And, (B) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
and, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; Or, (2) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.95, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from Appendix A to subpart B of part 429). (2) Alternative efficiency determination methods. In lieu of testing, a represented value of efficiency or consumption for a basic model of commercial warm air furnace must be determined through the application of an AEDM pursuant to the requirements of §429.70 and the provisions of this section, where: (i) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the output of the AEDM and less than or equal to the Federal standard for that basic model; and (ii) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the output of the AEDM and greater than or equal to the Federal standard for that basic model. (b) Certification reports. (1) The requirements of §429.12 are applicable to commercial warm air furnaces; and (2) Pursuant to §429.12(b)(13), a certification report must include the following public, equipmentspecific information: The thermal efficiency in percent (%), and the maximum rated input capacity in British thermal units per hour (Btu/h). (3) Pursuant to §429.12(b)(13), a certification report must include the following additional equipmentspecific information: (i) Whether the basic model is engineeredtoorder; and (ii) For any basic model rated with an AEDM, whether the manufacturer elects the witness test option for verification testing. (See §429.70(c)(5)(iii) for options). However, the manufacturer may not select more than 10% of AEDMrated basic models. (4) Pursuant to §429.12(b)(13), a certification report may include supplemental testing instructions in PDF format. If necessary to run a valid test, the equipmentspecific, supplemental information must include any additional testing and testing set up instructions (e.g., specific operational or control codes or settings), which would be necessary to operate the basic model under the required conditions specified by the relevant test procedure. A manufacturer may also include with a certification report other supplementary items in PDF format (e.g., manuals) for DOE consideration in performing testing under subpart C of this part. [79 FR 25500, May 5, 2014, as amended at 80 FR 151, Jan. 5, 2015] §429.42 Commercial refrigerators, freezers, and refrigeratorfreezers.(a) Determination of represented value. Manufacturers must determine the represented value, which includes the certified rating, for each basic model of commercial refrigerator, freezer, or refrigeratorfreezer either by testing, in conjunction with the applicable sampling provisions, or by applying an AEDM. (1) Units to be tested. (i) If the represented value for a given basic model is determined through testing, the general requirements of §429.11 are applicable; and (ii) For each basic model selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
And x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (2) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n1 degrees of freedom (from Appendix A to subpart B of part 429); And, (B) Any represented value of the energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
And, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (2) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n1 degrees of freedom (from Appendix A to subpart B of part 429). (2) Alternative efficiency determination methods. In lieu of testing, a represented value of efficiency or consumption for a basic model of commercial refrigerator, freezer or refrigeratorfreezer must be determined through the application of an AEDM pursuant to the requirements of §429.70 and the provisions of this section, where: (i) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the output of the AEDM and less than or equal to the Federal standard for that basic model; and (ii) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the output of the AEDM and greater than or equal to the Federal standard for that basic model. (b) Certification reports. (1) The requirements of §429.12 are applicable to commercial refrigerators, freezers, and refrigeratorfreezers; and (2) Pursuant to §429.12(b)(13), a certification report must include the following public, equipmentspecific information: (i) The daily energy consumption in kilowatt hours per day (kWh/day); (ii) The rating temperature (e.g. lowest product application temperature, if applicable) in degrees Fahrenheit ( °F); and (iii) The chilled or frozen compartment volume in cubic feet (ft3), the adjusted volume in cubic feet (ft3), or the total display area (TDA) in feet squared (ft2) (as appropriate for the equipment class). (3) Pursuant to §429.12(b)(13), a certification report must include the following additional, equipmentspecific information: (i) Whether the basic model is engineeredtoorder; and (ii) For any basic model rated with an AEDM, whether the manufacturer elects the witness test option for verification testing. (See §429.70(c)(5)(iii) for options). However, the manufacturer may not select more than 10% of AEDMrated basic models. (4) Pursuant to §429.12(b)(13), a certification report must include supplemental information submitted in PDF format. The equipmentspecific, supplemental information must include any additional testing and testing set up instructions (e.g., charging instructions) for the basic model; identification of all special features that were included in rating the basic model; and all other information (e.g., any specific settings or controls) necessary to operate the basic model under the required conditions specified by the relevant test procedure. A manufacturer may also include with a certification report other supplementary items in PDF format (e.g., manuals) for DOE to consider when performing testing under subpart C of this part. [76 FR 12451, Mar. 7, 2011; 76 FR 24775, May 2, 2011, as amended at 76 FR 38292, June 30, 2011; 78 FR 79593, Dec. 31, 2013; 79 FR 22307, Apr. 21, 2014; 79 FR 25501, May 5, 2014; 80 FR 151, Jan. 5, 2015] §429.43 Commercial heating, ventilating, air conditioning (HVAC) equipment.Link to an amendment published at 80 FR 37147, June 30, 2015. (a) Determination of represented value. Manufacturers must determine the represented value, which includes the certified rating, for each basic model of commercial HVAC equipment either by testing, in conjunction with the applicable sampling provisions, or by applying an AEDM. (1) Units to be tested. (i) If the represented value is determined through testing, the general requirements of §429.11 are applicable; and (ii) For each basic model selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
And, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (2) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n1 degrees of freedom (from Appendix A to subpart B of part 429). And, (B) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
And, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (2) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.95, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n1 degrees of freedom (from Appendix A to subpart B of part 429). (2) Alternative efficiency determination methods. In lieu of testing, a represented value of efficiency or consumption for a basic model of commercial HVAC equipment must be determined through the application of an AEDM pursuant to the requirements of §429.70 and the provisions of this section, where: (i) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the output of the AEDM and less than or equal to the Federal standard for that basic model; and (ii) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the output of the AEDM and greater than or equal to the Federal standard for that basic model. (b) Certification reports. (1) The requirements of §429.12 are applicable to commercial HVAC equipment; and (2) Pursuant to §429.12(b)(13), a certification report must include the following public equipmentspecific information: (i) Commercial package airconditioning equipment (except commercial package air conditioning that are aircooled with a cooling capacity less than 65,000 Btu/h): The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), the rated cooling capacity in British thermal units per hour (Btu/h), and the type(s) of heating used by the basic model (e.g., electric, gas, hydronic, none). (ii) Commercial package heating equipment (except commercial package heating equipment that is aircooled with a cooling capacity less than 65,000 Btu/h): The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), the coefficient of performance (COP), the rated cooling capacity in British thermal units per hour (Btu/h), and the type(s) of heating used by the basic model (e.g., electric, gas, hydronic, none). (iii) Commercial package air conditioning equipment that is aircooled with a cooling capacity less than 65,000 Btu/h (3Phase): The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)), and the rated cooling capacity in British thermal units per hour (Btu/h). (iv) Commercial package heating equipment that is aircooled with a cooling capacity less than 65,000 Btu/h (3Phase): The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)), the heating seasonal performance factor (HSPF in British thermal units per Watthour (Btu/Wh)), and the rated cooling capacity in British thermal units per hour (Btu/h). (v) Package terminal air conditioners: The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), the rated cooling capacity in British thermal units per hour (Btu/h), and the wall sleeve dimensions in inches (in). (vi) Package terminal heat pumps: The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), the coefficient of performance (COP), the rated cooling capacity in British thermal units per hour (Btu/h), and the wall sleeve dimensions in inches (in). (vii) Single package vertical air conditioners: The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)) and the rated cooling capacity in British thermal units per hour (Btu/h). (viii) Single package vertical heat pumps: The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), the coefficient of performance (COP), and the rated cooling capacity in British thermal units per hour (Btu/h). (ix) Variable refrigerant flow multisplit air conditioners with rated cooling capacity less than 65,000 Btu/h (3Phase): The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)) and rated cooling capacity in British thermal units per hour (Btu/h). (x) Variable refrigerant flow multisplit heat pumps with rated cooling capacity less than 65,000 Btu/h (3Phase): The seasonal energy efficiency ratio (SEER in British thermal units per Watthour (Btu/Wh)), the heating seasonal performance factor (HSPF in British thermal units per Watthour (Btu/Wh)), and rated cooling capacity in British thermal units per hour (Btu/h). (xi) Variable refrigerant flow multisplit air conditioners with rated cooling capacity greater than or equal to 65,000 Btu/h: The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), rated cooling capacity in British thermal units per hour (Btu/h), and the type(s) of heating used by the basic model (e.g., electric, gas, hydronic, none). (xii) Variable refrigerant flow multisplit heat pumps with rated cooling capacity greater than or equal to 65,000 Btu/h: The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), the coefficient of performance (COP), rated cooling capacity in British thermal units per hour (Btu/h), and the type(s) of heating used by the basic model (e.g., electric, gas, hydronic, none). (xiii) Water source variable refrigerant flow heat pumps (all rated cooling capacities): The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), the coefficient of performance (COP), rated cooling capacity in British thermal units per hour (Btu/h), and the type(s) of heating used by the basic model (e.g., electric, gas, hydronic, none). (xiv) Computer room airconditioners: The net sensible cooling capacity in British thermal units per hour (Btu/h), the net cooling capacity in British thermal units per hour (Btu/h), the configuration (upflow/downflow), economizer presence (yes or no), condenser medium (air, water, or glycolcooled), sensible coefficient of performance (SCOP), and rated airflow in standard cubic feet per minute (SCFM). (xv) Water source heat pumps (other than variable refrigerant flow): The energy efficiency ratio (EER in British thermal units per Watthour (Btu/Wh)), the coefficient of performance (COP), the rated cooling capacity in British thermal units per hour (Btu/h), and the type(s) of heating used by the basic model (e.g., electric, gas, hydronic, none). (3) Pursuant to §429.12(b)(13), a certification report must include the following additional equipmentspecific information: (i) Whether the basic model is engineeredtoorder; and (ii) For any basic model rated with an AEDM, whether the manufacturer elects the witness test option for verification testing. (See §429.70(c)(5)(iii) for options). However, the manufacturer may not select more than 10% of AEDMrated basic models. (4) Pursuant to §429.12(b)(13), a certification report must include supplemental information submitted in PDF format. The equipmentspecific, supplemental information must include any additional testing and testing set up instructions (e.g., charging instructions) for the basic model; identification of all special features that were included in rating the basic model; and all other information (e.g., operational codes or component settings) necessary to operate the basic model under the required conditions specified by the relevant test procedure. A manufacturer may also include with a certification report other supplementary items in PDF format (e.g., manuals) for DOE consideration in performing testing under subpart C of this part. The equipmentspecific, supplemental information must include at least the following: (i) Commercial package airconditioning equipment (except commercial package air conditioning equipment that is aircooled with a cooling capacity less than 65,000 Btu/h): The nominal cooling capacity in British thermal units per hour (Btu/h); rated airflow in standard cubic feet per minute (SCFM) for each fan coil; water flow rate in gallons per minute (gpm) for water cooled units only; rated static pressure in inches of water; refrigeration charging instructions (e.g., refrigerant charge, superheat and/or subcooling temperatures); frequency or control set points for variable speed components (e.g., compressors, VFDs); required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions, if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. (ii) Commercial package heating equipment (except commercial package heating equipment that is aircooled with a cooling capacity less than 65,000 Btu/h): The nominal cooling capacity in British thermal units per hour (Btu/h); rated heating capacity in British thermal units per hour (Btu/h); rated airflow in standard cubic feet per minute (SCFM) for each fan coil; water flow rate in gallons per minute (gpm) for water cooled units only; rated static pressure in inches of water; refrigeration charging instructions (e.g., refrigerant charge, superheat and/or subcooling temperatures); frequency or control set points for variable speed components (e.g., compressors, VFDs); required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions, if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. (iii) Commercial package air conditioning equipment that is aircooled with a cooling capacity less than 65,000 Btu/h (3phase): The nominal cooling capacity in British thermal units per hour (Btu/h); rated airflow in standard cubic feet per minute (SCFM) for each fan coil; rated static pressure in inches of water; refrigeration charging instructions (e.g., refrigerant charge, superheat and/or subcooling temperatures); frequency or control set points for variable speed components (e.g., compressors, VFDs); required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions, if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. (iv) Commercial package heating equipment that is aircooled with a cooling capacity less than 65,000 Btu/h (3phase): The nominal cooling capacity in British thermal units per hour (Btu/h); rated heating capacity in British thermal units per hour (Btu/h); rated airflow in standard cubic feet per minute (SCFM) for each fan coil; rated static pressure in inches of water; refrigeration charging instructions (e.g., refrigerant charge, superheat and/or subcooling temperatures); frequency or control set points for variable speed components (e.g., compressors, VFDs); required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions, if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. (v) Variable refrigerant flow multisplit air conditioners with cooling capacity less than 65,000 Btu/h (3phase): The nominal cooling capacity in British thermal units per hour (Btu/h); outdoor unit(s) and indoor units identified in the tested combination; components needed for heat recovery, if applicable; rated airflow in standard cubic feet per minute (SCFM) for each indoor unit; water flow rate in gallons per minute (gpm) for watercooled units only; rated static pressure in inches of water; compressor frequency set points; required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions, if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. Additionally, upon DOE request, the manufacturer must provide a layout of the system setup for testing including charging instructions consistent with the installation manual. (vi) Variable refrigerant flow multisplit heat pumps with cooling capacity less than 65,000 Btu/h (3phase): The nominal cooling capacity in British thermal units per hour (Btu/h); rated heating capacity in British thermal units per hour (Btu/h); outdoor unit(s) and indoor units identified in the tested combination; components needed for heat recovery, if applicable; rated airflow in standard cubic feet per minute (SCFM) for each indoor unit; water flow rate in gallons per minute (gpm) for watercooled units only; rated static pressure in inches of water; compressor frequency set points; required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions, if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. Additionally, upon DOE request, the manufacturer must provide a layout of the system setup for testing including charging instructions consistent with the installation manual. (vii) Variable refrigerant flow multisplit air conditioners with cooling capacity greater than or equal to 65,000 Btu/h: The nominal cooling capacity in British thermal units per hour (Btu/h); outdoor unit(s) and indoor units identified in the tested combination; components needed for heat recovery, if applicable; rated airflow in standard cubic feet per minute (SCFM) for each indoor unit; water flow rate in gallons per minute (gpm) for watercooled units only; rated static pressure in inches of water; compressor frequency set points; required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. Additionally, upon DOE request, the manufacturer must provide a layout of the system setup for testing including charging instructions consistent with the installation manual. (viii) Variable refrigerant flow multisplit heat pumps with cooling capacity greater than or equal to 65,000 Btu/h: The nominal cooling capacity in British thermal units per hour (Btu/h); rated heating capacity in British thermal units per hour (Btu/h); outdoor unit(s) and indoor units identified in the tested combination; components needed for heat recovery, if applicable; rated airflow in standard cubic feet per minute (SCFM) for each indoor unit; water flow rate in gallons per minute (gpm) for watercooled units only; rated static pressure in inches of water; compressor frequency set points; required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. Additionally, upon DOE request, the manufacturer must provide a layout of the system setup for testing including charging instructions consistent with the installation manual. (ix) Water source variable refrigerant flow heat pumps: The nominal cooling capacity in British thermal units per hour (Btu/h); rated heating capacity in British thermal units per hour (Btu/h); rated airflow in standard cubic feet per minute (SCFM) for each indoor unit; water flow rate in gallons per minute (gpm); rated static pressure in inches of water; refrigeration charging instructions (e.g., refrigerant charge, superheat and/or subcooling temperatures); frequency set points for variable speed components (e.g., compressors, VFDs), including the required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. Additionally, upon DOE request, the manufacturer must provide a layout of the system setup for testing including charging instructions consistent with the installation manual. (x) Water source heat pumps: The nominal cooling capacity in British thermal units per hour (Btu/h); rated heating capacity in British thermal units per hour (Btu/h); rated airflow in standard cubic feet per minute (SCFM) for each indoor unit; water flow rate in gallons per minute (gpm); rated static pressure in inches of water; refrigerant charging instructions, (e.g., refrigerant charge, superheat and/or subcooling temperatures); frequency set points for variable speed components (e.g., compressors, VFDs), including the required dip switch/control settings for step or variable components; a statement whether the model will operate at test conditions without manufacturer programming; any additional testing instructions if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. (xi) Single package vertical air conditioners: Any additional testing instructions, if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. (xii) Single package vertical heat pumps: Any additional testing instructions, if applicable; if a variety of motors/drive kits are offered for sale as options in the basic model to account for varying installation requirements, the model number and specifications of the motor (to include efficiency, horsepower, open/closed, and number of poles) and the drive kit, including settings, associated with that specific motor that were used to determine the certified rating; and which, if any, special features were included in rating the basic model. (xiii) Computer room airconditioners: Any additional testing instructions, if applicable; and which, if any, special features were included in rating the basic model. (xiv) Package terminal air conditioners and package terminal heat pumps: Any additional testing instructions, if applicable. (c) Alternative methods for determining efficiency or energy use for commercial HVAC equipment can be found in §429.70 of this subpart. [76 FR 12451, Mar. 7, 2011; 76 FR 24775, May 2, 2011, as amended at 78 FR 79594, Dec. 31, 2013; 79 FR 25501, May 5, 2014; 80 FR 151, Jan. 5, 2015] §429.44 Commercial water heating equipment.Link to an amendment published at 79 FR 40565, July 11, 2014. (a) Determination of represented value. Manufacturers must determine the represented value, which includes the certified rating, for each basic model of commercial water heating equipment, either by testing, in conjunction with the applicable sampling provisions, or by applying an AEDM. (1) Units to be tested. (i) If the represented value for a given basic model is determined through testing, the general requirements of §429.11 are applicable; and (ii) For each basic model selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
And, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (2) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n1 degrees of freedom (from Appendix A to subpart B of part 429). And, (B) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
And, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (2) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.95, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n1 degrees of freedom (from Appendix A to subpart B of part 429). (2) Alternative efficiency determination methods. In lieu of testing, a represented value of efficiency or consumption for a basic model of commercial water heating equipment must be determined through the application of an AEDM pursuant to the requirements of §429.70 and the provisions of this section, where: (i) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the output of the AEDM and less than or equal to the Federal standard for that basic model; and (ii) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the output of the AEDM and greater than or equal to the Federal standard for that basic model. (b) Certification reports. (1) The requirements of §429.12 are applicable to commercial WH equipment; and (2) Pursuant to §429.12(b)(13), a certification report must include the following public equipmentspecific information: (i) Commercial electric storage water heaters: The maximum standby loss in percent per hour (%/hr) and the measured storage volume in gallons (gal). (ii) Commercial gasfired and oilfired storage water heaters: The thermal efficiency in percent (%), the maximum standby loss in British thermal units per hour (Btu/h), the rated storage volume in gallons (gal), and the nameplate input rate in British thermal units per hour (Btu/h). (iii) Commercial water heaters and hot water supply boilers with storage capacity greater than 140 gallons: The thermal efficiency in percent (%), whether the storage volume is greater than 140 gallons (Yes/No); whether the tank surface area is insulated with at least R12.5 (Yes/No); whether a standing pilot light is used (Yes/No); for gas or oilfired water heaters, whether the basic model has a fire damper or fan assisted combustion (Yes/No); and, if applicable, pursuant to 10 CFR 431.110, the maximum standby loss in British thermal units per hour (Btu/h) and measured storage volume in gallons (gal). (iv) Commercial gasfired and oilfired instantaneous water heaters greater than or equal to 10 gallons and gasfired and oilfired hot water supply boilers greater than or equal to 10 gallons: The thermal efficiency in percent (%), the maximum standby loss in British thermal units per hour (Btu/h), the rated storage volume in gallons (gal), and the nameplate input rate in Btu/h. (v) Commercial gasfired and oilfired instantaneous water heaters less than 10 gallons and gasfired and oilfired hot water supply boilers less than 10 gallons: The thermal efficiency in percent (%) and the rated storage volume in gallons (g). (vi) Commercial unfired hot water storage tanks: The thermal insulation (i.e., Rvalue) and stored volume in gallons (gal). (3) Pursuant to §429.12(b)(13), a certification report must include the following additional, equipmentspecific information: (i) Whether the basic model is engineeredtoorder; and (ii) For any basic model rated with an AEDM, whether the manufacturer elects the witness test option for verification testing. (See §429.70(c)(5)(iii) for options). However, the manufacturer may not select more than 10% of AEDMrated basic models to be eligible for witness testing. (4) Pursuant to §429.12(b)(13), a certification report may include supplemental testing instructions in PDF format. If necessary to run a valid test, the equipmentspecific, supplemental information must include any additional testing and testing set up instructions (e.g., whether a bypass loop was used for testing) for the basic model and all other information (e.g., operational codes or overrides for the control settings) necessary to operate the basic model under the required conditions specified by the relevant test procedure. A manufacturer may also include with a certification report other supplementary items in PDF format (e.g., manuals) for DOE consideration in performing testing under subpart C of this part. (c) Alternative methods for determining efficiency or energy use for commercial WH equipment can be found in §429.70 of this subpart. [76 FR 12451, Mar. 7, 2011; 76 FR 24776, May 2, 2011, as amended at 78 FR 79594, Dec. 31, 2013; 79 FR 25504, May 5, 2014; 80 FR 151, Jan. 5, 2015] §429.45 Automatic commercial ice makers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to automatic commercial ice makers; and (2) For each basic model of automatic commercial ice maker selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of maximum energy use or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and (ii) Any represented value of the energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to automatic commercial ice makers; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The maximum energy use in kilowatt hours per 100 pounds of ice (kWh/100 lbs ice), the maximum condenser water use in gallons per 100 pounds of ice (gal/100 lbs ice), the harvest rate in pounds of ice per 24 hours (lbs ice/24 hours), the type of cooling, and the equipment type. [76 FR 12451, Mar. 7, 2011; 76 FR 24776, May 2, 2011] §429.46 Commercial clothes washers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to commercial clothes washers; and (2) For each basic model of commercial clothes washers, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of the water factor or other measure of energy or water consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 971⁄2 percent confidence limit (UCL) of the true mean divided by 1.05, where:
and (ii) Any represented value of the modified energy factor or other measure of energy or water consumption of a basic model for which consumers would favor higher values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The lower 971⁄2 percent confidence limit (LCL) of the true mean divided by 0.95, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to commercial clothes washers; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) If testing was conducted using Appendix J1 to subpart B of part 430 of this chapter: The modified energy factor (MEF) in cubic feet per kilowatt hour per cycle (cu ft/kWh/cycle); and the water factor (WF) in gallons per cubic feet per cycle (gal/cu ft/cycle); (ii) If testing was conducted using Appendix J2 to subpart B of part 430 of this chapter: The modified energy factor (MEFJ2) in cu ft/kWh/cycle and the integrated water factor (IWF) in gal/cu ft/cycle. [76 FR 12451, Mar. 7, 2011; 76 FR 24777, May 2, 2011, as amended at 79 FR 71630, Dec. 3, 2014] §429.47 Distribution transformers.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to distribution transformers; and (2) For each basic model of distribution transformer, efficiency must be determined either by testing, in accordance with §431.193 and the provisions of this section, or by application of an AEDM that meets the requirements of §429.70 and the provisions of this section. (i) For each basic model selected for testing: (A) If the manufacturer produces five or fewer units of a basic model over 6 months, each unit must be tested. A manufacturer may not use a basic model with a sample size of fewer than five units to substantiate an AEDM pursuant to §429.70. (B) If the manufacturer produces more than five units over 6 months, a sample of at least five units must be selected and tested. (ii) Any represented value of efficiency of a basic model must satisfy the condition:
(b) Certification reports. (1) The requirements of §429.12 are applicable to distribution transformers except that required information in paragraph (b) of this section may be reported by kVA grouping instead of by basic model and paragraph (b)(6) of this section does not apply; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: For the most and least efficient basic models within each “kVA grouping” for which part 431 prescribes an efficiency standard, the kVA rating, the insulation type (i.e., lowvoltage drytype, mediumvoltage drytype or liquidimmersed), the number of phases (i.e., singlephase or threephase), and the basic impulse insulation level (BIL) group rating (for mediumvoltage drytypes). (c) Alternative methods for determining efficiency or energy use for distribution transformers can be found in §429.70 of this subpart. (d) Kilovolt ampere (kVA) grouping. As used in this section, a “kVA grouping” is a group of basic models which all have the same kVA rating, have the same insulation type (i.e., lowvoltage drytype, mediumvoltage drytype or liquidimmersed), have the same number of phases (i.e., singlephase or threephase), and, for mediumvoltage drytypes, have the same BIL group rating (i.e., 2045 kV BIL, 4695 kV BIL or greater than or equal to96 kV BIL). §429.48 Illuminated exit signs.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to illuminated exit signs; and (2) For each basic model of illuminated exit sign selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of input power demand or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A)The mean of the sample, where:
Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and (ii) Any represented value of the energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to illuminated exit signs; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The input power demand in watts (W) and the number of faces. [76 FR 12451, Mar. 7, 2011; 76 FR 24778, May 2, 2011] §429.49 Traffic signal modules and pedestrian modules.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to traffic signal modules and pedestrian modules; and (2) For each basic model of traffic signal module or pedestrian module selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of estimated maximum and nominal wattage or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and (ii) Any represented value of the energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to traffic signal modules and pedestrian modules; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The maximum wattage at 74 degrees Celsius (°C) in watts (W), the nominal wattage at 25 degrees Celsius (°C) in watts (W), and the signal type. [76 FR 12451, Mar. 7, 2011; 76 FR 24778, May 2, 2011] §429.50 Commercial unit heaters.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to commercial unit heaters; and (2) [Reserved] (b) Certification reports. (1) The requirements of §429.12 are applicable to commercial unit heaters; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The type of ignition system and a declaration that the manufacturer has incorporated the applicable design requirements. §429.51 Commercial prerinse spray valves.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to commercial prerinse spray valves; and (2) For each basic model of commercial prerinse spray valves selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of water consumption or other measure of water consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and (ii) Any represented value of the water efficiency or other measure of water consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to commercial prerinse spray valves; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The maximum flow rate in gallons per minute (gpm), rounded to the nearest 0.1 gallon. [76 FR 12451, Mar. 7, 2011; 76 FR 24779, May 2, 2011, as amended at 78 FR 62986, Oct. 23, 2013] §429.52 Refrigerated bottled or canned beverage vending machines.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to refrigerated bottled or canned beverage vending machine; and (2) For each basic model of refrigerated bottled or canned beverage vending machine selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (i) Any represented value of energy consumption or other measure of energy consumption of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (A) The mean of the sample, where:
Or, (B) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.10, where:
and (ii) Any represented value of the energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.90, where:
(b) Certification reports. (1) The requirements of §429.12 are applicable to refrigerated bottled or canned beverage vending machine; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The maximum average daily energy consumption in kilowatt hours per day (kWh/day), the refrigerated volume (V) in cubic feet (ft3) used to demonstrate compliance with standards set forth in §431.296, the ambient temperature in degrees Fahrenheit (°F), and the ambient relative humidity in percent (%) during the test. [76 FR 12451, Mar. 7, 2011; 76 FR 24779, May 2, 2011, as amended at 76 FR 38292, June 30, 2011] §429.53 Walkin coolers and walkin freezers.(a) Determination of represented value—(1) Refrigeration equipment: Manufacturers must determine the represented value, which includes the certified rating, for each basic model of walkin cooler or freezer refrigeration equipment, either by testing, in conjunction with the applicable sampling provisions, or by applying an AEDM satisfying the criteria provided at §429.70(f)(1). (i) Units to be tested. (A) If the represented value for a given basic model is determined through testing, the general requirements of §429.11 apply; and (B) For each basic model selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (1) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (i) The mean of the sample, where: and, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (ii) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where: And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from Appendix A to subpart B). And, (2) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (i) The mean of the sample, where: And, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (ii) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.95, where: And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from Appendix A to subpart B). (ii) Alternative efficiency determination methods. In lieu of testing, a represented value of efficiency or consumption for a basic model of a walkin cooler or freezer refrigeration system must be determined through the application of an AEDM pursuant to the requirements of §429.70 and the provisions of this section, where: (A) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the output of the AEDM and less than or equal to the Federal standard for that basic model; and (B) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the output of the AEDM and greater than or equal to the Federal standard for that basic model. (iii) If the represented value of a refrigeration system was determined using the unit cooler testing provisions at 10 CFR 431.304(c)(12), that represented value may be used for all refrigeration systems containing that unit cooler irrespective of whether such equipment is sold separately or as part of a matched refrigeration system. However, for any representations of matchedsystem efficiency that exceed the refrigeration system rating as determined by the unit cooler testing provisions at 10 CFR 431.304(c)(12) and for which a manufacturer wishes to make representations of the moreefficient rating, then the matched refrigeration system must be tested separately in accordance with the DOE test procedure for matched systems and applicable sampling plan. (2) WICF components other than those specified in (a)(1) of this section—(i) Units to be tested. (A) The general requirements of §429.11 apply; and (B) For each basic model selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (1) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (i) The mean of the sample, where: and, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (ii) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where: And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from Appendix A to subpart B). And, (2) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (i) The mean of the sample, where: And, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; or, (ii) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.95, where: And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from Appendix A to subpart B). (b) Certification reports. (1) The requirements of §429.12 are applicable to manufacturers of the components of walkin coolers and freezers (WICFs) listed in paragraph (b)(2) of this section, and; (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: (i) For WICF doors: The door type, Rvalue of the door insulation, and a declaration that the manufacturer has incorporated the applicable design requirements. In addition, for those WICFs with transparent reachin doors and windows: The glass type of the doors and windows (e.g., doublepane with heat reflective treatment, triplepane glass with gas fill), and the power draw of the antisweat heater in watts per square foot of door opening. (ii) For WICF panels: The Rvalue of the insulation (except for glazed portions of the doors or structural members). (iii) For WICF refrigeration systems: The motor's purpose (i.e., evaporator fan motor or condenser fan motor), the horsepower, and a declaration that the manufacturer has incorporated the applicable design requirements. [79 FR 27409, May 13, 2014] §429.54 Metal halide lamp ballasts and fixtures.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to metal halide lamp ballasts; and (2) For each basic model of metal halide lamp ballast selected for testing, a sample of sufficient size, not less than four, shall be selected at random and tested to ensure that: (i) Any represented value of estimated energy efficiency calculated as the measured output power to the lamp divided by the measured input power to the ballast (Pout/Pin), of a basic model is less than or equal to the lower of: (A) The mean of the sample, where:
Or, (B) The lower 99percent confidence limit (LCL) of the true mean divided by 0.99.
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.99 is the t statistic for a 99% twotailed confidence interval with n1 degrees of freedom (from appendix A). (b) Certification reports. (1) The requirements of §429.12 are applicable to metal halide lamp ballasts; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The minimum ballast efficiency in percent (%), the lamp wattage in watts (W), and the type of ballast (e.g., pulsestart, magnetic probestart, and nonpulse start electronic). [76 FR 12451, Mar. 7, 2011; 76 FR 24780, May 2, 2011; 76 FR 46202, Aug. 2, 2011] §429.58 Furnace fans.(a) Sampling plan for selection of units for testing. (1) The requirements of §429.11 are applicable to furnace fans; and (2) For each basic model of furnace fan within the scope of appendix AA of subpart B of part 430, a sample of sufficient size shall be randomly selected and tested to ensure that any represented value of fan energy rating (FER), rounded to the nearest integer, shall be greater than or equal to the higher of: (i) The mean of the sample, where: And, x̅ is the sample mean; n is the number of samples; and xi is the measured value for the ith sample; Or, (ii) The upper 90 percent confidence limit (UCL) of the true mean divided by 1.05, where: And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.90 is the t statistic for a 90% onetailed confidence interval with n1 degrees of freedom (from Appendix A). (b) Certification reports. (1) The requirements of §429.12 are applicable to residential furnace fans; and (2) Pursuant to §429.12(b)(13), a certification report shall include the following public productspecific information: The fan energy rating (FER) in watts per thousand cubic feet per minute (W/1000 cfm); the calculated maximum airflow at the reference system external static pressure (ESP) in cubic feet per minute (cfm); the control system configuration for achieving the heating and constantcirculation airflowcontrol settings required for determining FER as specified in the furnace fan test procedure (10 CFR part 430, subpart B, appendix AA); the measured steadystate gas, oil, or electric heat input rate (QIN) in the heating setting required for determining FER; and for modular blowers, the manufacturer and model number of the electric heat resistance kit with which it is equipped for certification testing. [79 FR 520, Jan. 3, 2014, as amended at 79 FR 38208, July 3, 2014] §429.60 Commercial packaged boilers.(a) Determination of represented value. Manufacturers must determine the represented value, which includes the certified rating, for each basic model of commercial packaged boilers either by testing, in conjunction with the applicable sampling provisions, or by applying an AEDM. (1) Units to be tested. (i) If the represented value is determined through testing, the general requirements of §429.11 are applicable; and (ii) For each basic model selected for testing, a sample of sufficient size shall be randomly selected and tested to ensure that— (A) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the higher of: (1) The mean of the sample, where:
and, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; Or, (2) The upper 95 percent confidence limit (UCL) of the true mean divided by 1.05, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from Appendix A to subpart B of part 429). And, (B) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the lower of: (1) The mean of the sample, where:
and, x̅ is the sample mean; n is the number of samples; and xi is the ith sample; Or, (2) The lower 95 percent confidence limit (LCL) of the true mean divided by 0.95, where:
And x̅ is the sample mean; s is the sample standard deviation; n is the number of samples; and t0.95 is the t statistic for a 95% onetailed confidence interval with n−1 degrees of freedom (from Appendix A to subpart B of part 429). (2) Alternative efficiency determination methods. In lieu of testing, a represented value of efficiency or consumption for a basic model of commercial packaged boiler must be determined through the application of an AEDM pursuant to the requirements of §429.70 and the provisions of this section, where: (i) Any represented value of energy consumption or other measure of energy use of a basic model for which consumers would favor lower values shall be greater than or equal to the output of the AEDM and less than or equal to the Federal standard for that basic model; and (ii) Any represented value of energy efficiency or other measure of energy consumption of a basic model for which consumers would favor higher values shall be less than or equal to the output of the AEDM and greater than or equal to the Federal standard for that basic model. (b) Certification reports. (1) The requirements of §429.12 are applicable to commercial packaged boilers; and (2) Pursuant to §429.12(b)(13), a certification report must include the following public equipmentspecific information: The combustion efficiency in percent (%) or the thermal efficiency in percent (%), as required in §431.87 of this chapter; and the maximum rated input capacity in British thermal units per hour (Btu/h). (3) Pursuant to §429.12(b)(13), a certification report must include the following additional equipmentspecific information: (i) Whether the basic model is engineeredtoorder; and (ii) For any basic model rated with an AEDM, whether the manufacturer elects the witness test option for verification testing. (See §429.70(c)(5)(iii) for options). However, the manufacturer may not select more than 10% of AEDMrated basic models to be eligible for witness testing. (4) Pursuant to §429.12(b)(13), a certification report may include supplemental testing instructions in PDF format. If necessary to run a valid test, the equipmentspecific, supplemental information must include any additional testing and testing set up instructions (e.g., specific operational or control codes or settings), which would be necessary to operate the basic model under the required conditions specified by the relevant test procedure. A manufacturer may also include with a certification report other supplementary items in PDF format (e.g., manuals) for DOE consideration in performing testing under subpart C of this part. (c) Alternative methods for determining efficiency or energy use for commercial packaged boilers can be found in §429.70. [79 FR 25504, May 5, 2014, as amended at 80 FR 151, Jan. 5, 2015] §429.70 Alternative methods for determining energy efficiency and energy use.Link to an amendment published at 79 FR 40565, July 11, 2014. (a) General applicability of an AEDM. A manufacturer of covered products or covered equipment explicitly authorized to use an AEDM in §§429.14 through 429.54 may not distribute any basic model of such equipment in commerce unless the manufacturer has determined the energy efficiency of the basic model, either from testing the basic model in conjunction with DOE's certification sampling plans and statistics or from applying an alternative method for determining energy efficiency or energy use (AEDM) to the basic model, in accordance with the requirements of this section. In instances where a manufacturer has tested a basic model, the manufacturer may not knowingly use an AEDM to overrate the efficiency (or underrate the consumption) of the model. (b) Testing. Testing for each covered product or covered equipment must be done in accordance with the sampling plan provisions established in §429.11 and the testing procedures in parts 430 and 431 of this chapter. (c) Alternative efficiency determination method (AEDM) for commercial HVAC (includes commercial warm air furnaces and commercial packaged boilers), WH, and refrigeration equipment—(1) Criteria an AEDM must satisfy. A manufacturer may not apply an AEDM to a basic model to determine its efficiency pursuant to this section unless: (i) The AEDM is derived from a mathematical model that estimates the energy efficiency or energy consumption characteristics of the basic model as measured by the applicable DOE test procedure; (ii) The AEDM is based on engineering or statistical analysis, computer simulation or modeling, or other analytic evaluation of performance data; and (iii) The manufacturer has validated the AEDM, in accordance with paragraph (c)(2) of this section with basic models that meet the current Federal energy conservation standards. (2) Validation of an AEDM. Before using an AEDM, the manufacturer must validate the AEDM's accuracy and reliability as follows: (i) The manufacturer must select at least the minimum number of basic models for each validation class specified in paragraph (c)(2)(iv) of this section to which the particular AEDM applies. Using the AEDM, calculate the energy use or efficiency for each of the selected basic models. Test a single unit of each selected basic model in accordance with paragraph (c)(2)(iii) of this section. Compare the results from the single unit test and the AEDM energy use or efficiency output according to paragraph (c)(2)(ii) of this section. The manufacturer is responsible for ensuring the accuracy and reliability of the AEDM. (ii) Individual model tolerances. (A) For those covered products with an energyefficiency metric, the predicted efficiency for each model calculated by applying the AEDM may not be more than five percent greater than the efficiency determined from the corresponding test of the model. (B) For those covered products with an energyconsumption metric, the predicted energy consumption for each model, calculated by applying the AEDM, may not be more than five percent less than the energy consumption determined from the corresponding test of the model. (C) For all covered products, the predicted energy efficiency or consumption for each model calculated by applying the AEDM must meet or exceed the applicable federal energy conservation performance standard. (iii) Additional test unit requirements. (A) Each AEDM must be supported by test data obtained from physical tests of current models; and (B) Test results used to validate the AEDM must meet or exceed current, applicable Federal standards as specified in part 431 of this chapter; and (C) Each test must have been performed in accordance with the DOE test procedure specified in parts 430 or 431 of this chapter or test procedure waiver for which compliance is required at the time the basic model is distributed in commerce. (iv) Validation classes.
^{1}The minimum number of tests indicated above must be comprised of a transparent model, a solid model, a vertical model, a semivertical model, a horizontal model, and a serviceoverthe counter model, as applicable based on the equipment offering. However, manufacturers do not need to include all types of these models if it will increase the minimum number of tests that need to be conducted. (3) AEDM records retention requirements. If a manufacturer has used an AEDM to determine representative values pursuant to this section, the manufacturer must have available upon request for inspection by the Department records showing: (i) The AEDM, including the mathematical model, the engineering or statistical analysis, and/or computer simulation or modeling that is the basis of the AEDM; (ii) Product information, complete test data, AEDM calculations, and the statistical comparisons from the units tested that were used to validate the AEDM pursuant to paragraph (c)(2) of this section; and (iii) Product information and AEDM calculations for each basic model to which the AEDM has been applied. (4) Additional AEDM requirements. If requested by the Department and at DOE's discretion, the manufacturer must perform at least one of the following: (i) Conduct simulations before representatives of the Department to predict the performance of particular basic models of the product to which the AEDM was applied; (ii) Provide analyses of previous simulations conducted by the manufacturer; or (iii) Conduct certification testing of basic models selected by the Department. (5) AEDM verification testing. DOE may use the test data for a given individual model generated pursuant to §429.104 to verify the certified rating determined by an AEDM as long as the following process is followed: (i) Selection of units. DOE will obtain units for test from retail, where available. If units cannot be obtained from retail, DOE will request that a unit be provided by the manufacturer; (ii) Lab requirements. DOE will conduct testing at an independent, thirdparty testing facility of its choosing. In cases where no thirdparty laboratory is capable of testing the equipment, it may be tested at a manufacturer's facility upon DOE's request. (iii) Manufacturer participation. (A) Except when testing variable refrigerant flow systems (which are governed by the rules found at §431.96(f)), testing will be completed without a manufacturer representative onsite. In limited instances further described in paragraph (c)(5)(iii)(B) of this section, a manufacturer and DOE representative may be present to witness the test setup. (B) A manufacturer's representative may request to be onsite to witness the test setup if: (1) The installation manual for the basic model specifically requires it to be started only by a factorytrained installer; or (2) The manufacturer has elected, as part of the certification of that basic model, to have the opportunity to witness the test setup. A manufacturer may elect to witness the test setup for the initial verification test for no more than 10 percent of the manufacturer's basic models submitted for certification and rated with an AEDM per validation class specified in section (c)(2)(iv) of this paragraph. The 10percent limit applies to all of the eligible basic models submitted for certification by a given manufacturer no matter how many AEDMs a manufacturer has used to develop its ratings. The 10percent limit is determined by first calculating 10 percent of the total number of basic models rated with an AEDM per validation class, and then truncating the resulting product. Manufacturers who have submitted fewer than 10 basic models rated with an AEDM for certification may elect to have the opportunity to witness the test setup of one basic model. A manufacturer must identify the basic models it wishes to witness as part of its certification report(s) prior to the basic model being selected for verification testing. (3) In those instances in which a manufacturer has not provided the required information as specified in §429.12(b)(13) for a given basic model that has been rated and certified as compliant with the applicable standards, a manufacturer is precluded from witnessing the testing set up for that basic model. (C) A DOE representative will be present for the test setup in all cases where a manufacturer representative requests to be onsite for the test setup. The manufacturer's representative cannot communicate with a lab representative outside of the DOE representative's presence. (D) If DOE has obtained through retail channels a unit for test that meets either of the conditions in paragraph (c)(5)(iii)(B) of this section, DOE will notify the manufacturer that the basic model was selected for testing and that the manufacturer may have a representative present for the test setup. If the manufacturer does not respond within five calendar days of receipt of that notification, the manufacturer waives the option to be present for test setup, and DOE will proceed with the test setup without a manufacturer's representative present. (E) If DOE has obtained directly from the manufacturer a unit for test that meets either of the conditions in paragraph (c)(5)(iii)(B) of this section, DOE will notify the manufacturer of the option to be present for the test setup at the time the unit is purchased. DOE will specify the date (not less than five calendar days) by which the manufacturer must notify DOE whether a manufacturer's representative will be present. If the manufacturer does not notify DOE by the date specified, the manufacturer waives the option to be present for the test setup, and DOE will proceed with the test setup without a manufacturer's representative present. (F) DOE will review the certification submissions from the manufacturer that were on file as of the date DOE purchased a basic model (under paragraph (c)(5)(iii)(D) of this section) or the date DOE notifies the manufacturer that the basic model has been selected for testing (under paragraph (c)(5)(iii)(E) of this section) to determine if the manufacturer has indicated that it intends to witness the test setup of the selected basic model. DOE will also verify that the manufacturer has not exceeded the allowable limit of witness testing selections as specified in paragraph (c)(5)(iii)(B)(2) of this section. If DOE discovers that the manufacturer exceeded the limits specified in paragraph (c)(5)(iii)(B)(2), DOE will notify the manufacturer of this fact and deny its request to be present for the test setup of the selected basic model. The manufacturer must update its certification submission to ensure it has not exceeded the allowable limit of witness testing selections as specified in paragraph (c)(5)(iii)(B)(2) to be present at setup for future selections. At this time DOE will also review the supplemental PDF submission(s) for the selected basic model to determine that all necessary information has been provided to the Department. (G) If DOE determines, pursuant to paragraph (c)(5)(ii) of this section, that the model should be tested at the manufacturer's facility, a DOE representative will be present on site to observe the test setup and testing with the manufacturer's representative. All testing will be conducted at DOE's direction, which may include DOEcontracted personnel from a thirdparty lab, as well as the manufacturer's technicians. (H) As further explained in paragraph (c)(5)(v)(B) of this section, if a manufacturer's representative is present for the initial test setup for any reason, the manufacturer forfeits any opportunity to request a retest of the basic model. Furthermore, if the manufacturer requests to be onsite for test setup pursuant to paragraph (c)(5)(iii)(B) of this section but is not present on site, the manufacturer forfeits any opportunity to request a retest of the basic model. (iv) Testing. At no time during verification testing may the lab and the manufacturer communicate without DOE authorization. All verification testing will be conducted in accordance with the applicable DOE test procedure, as well as each of the following to the extent that they apply: (A) Any active test procedure waivers that have been granted for the basic model; (B) Any test procedure guidance that has been issued by DOE; (C) The installation and operations manual that is shipped with the unit; (D) Any additional information that was provided by the manufacturer at the time of certification (prior to DOE obtaining the unit for test); and (E) If during test setup or testing, the lab indicates to DOE that it needs additional information regarding a given basic model in order to test in accordance with the applicable DOE test procedure, DOE may organize a meeting between DOE, the manufacturer and the lab to provide such information. (v) Failure to meet certified rating. If a model tests worse than its certified rating by an amount exceeding the tolerance prescribed in paragraph (c)(5)(vi) of this section, DOE will notify the manufacturer. DOE will provide the manufacturer with all documentation related to the test set up, test conditions, and test results for the unit. Within the timeframe allotted by DOE, the manufacturer may then: (A) Present all claims regarding testing validity; and (B) If the manufacturer was not on site for the initial test setup, request a retest of the previously tested unit with manufacturer and DOE representatives onsite for the test setup. DOE will not conduct the retest using a different unit of the same basic model unless DOE and the manufacturer determine it is necessary based on the test results, claims presented, and DOE regulations. (vi) Tolerances. (A) For consumption metrics, the result from a DOE verification test must be less than or equal to the certified rating × (1 + the applicable tolerance). (B) For efficiency metrics, the result from a DOE verification test must be greater than or equal to the certified rating × (1 − the applicable tolerance).
(vii) Invalid rating. If, following discussions with the manufacturer and a retest where applicable, DOE determines that the verification testing was conducted appropriately in accordance with the DOE test procedure, DOE will issue a determination that the rating for the model is invalid. The manufacturer must elect, within 15 days, one of the following to be completed in a time frame specified by DOE, which is never to exceed 180 days: (A) Rerate and recertify the model based on DOE's test data alone; or (B) Discontinue the model through the certification process; or (C) Conduct additional testing and rerate and recertify the basic model based on all test data collected, including DOE's test data. (viii) AEDM use. (A) If DOE has determined that a manufacturer made invalid ratings on two or more models rated using the same AEDM within a 24 month period, the manufacturer must take the action listed in the table corresponding to the number of invalid certified ratings. The twentyfour month period begins with a DOE determination that a rating is invalid through the process outlined above. Additional invalid ratings apply for the purposes of determining the appropriate consequences if the subsequent determination(s) is based on selection of a unit for testing within the twentyfour month period (i.e., subsequent determinations need not be made within 24 months).
^{1}A manufacturer may discuss with DOE's Office of Enforcement whether existing test data on different basic models within the validation classes to which that specific AEDM was applied may be used to meet this requirement. ^{2}The “same AEDM” means a computer simulation or mathematical model that is identified by the manufacturer at the time of certification as having been used to rate a model or group of models. ^{3}The twentyfour month period begins with a DOE determination that a rating is invalid through the process outlined above. Additional invalid ratings apply for the purposes of determining the appropriate consequences if the subsequent determination(s) is based on testing of a unit that was selected for testing within the twentyfour month period (i.e., subsequent determinations need not be made within 24 months). (B) If, as a result of eight or more invalid ratings, a manufacturer has lost the privilege of using an AEDM for rating, the manufacturer may regain the ability to use an AEDM by: (1) Investigating and identifying cause(s) for failures; (2) Taking corrective action to address cause(s); (3) Performing six new tests per validation class, a minimum of two of which must be performed by an independent, thirdparty laboratory to validate the AEDM; and (4) Obtaining DOE authorization to resume use of the AEDM. (d) Alternative efficiency determination method for distribution transformers—A manufacturer may use an AEDM to determine the efficiency of one or more of its untested basic models only if it determines the efficiency of at least five of its other basic models (selected in accordance with paragraph (d)(3) of this section) through actual testing. (1) Criteria an AEDM must satisfy. (i) The AEDM has been derived from a mathematical model that represents the electrical characteristics of that basic model; (ii) The AEDM is based on engineering and statistical analysis, computer simulation or modeling, or other analytic evaluation of performance data; and (iii) The manufacturer has substantiated the AEDM, in accordance with paragraph (d)(2) of this section, by applying it to, and testing, at least five other basic models of the same type, i.e., lowvoltage drytype distribution transformers, mediumvoltage drytype distribution transformers, or liquidimmersed distribution transformers. (2) Substantiation of an AEDM. Before using an AEDM, the manufacturer must substantiate the AEDM's accuracy and reliability as follows: (i) Apply the AEDM to at least five of the manufacturer's basic models that have been selected for testing in accordance with paragraph (d)(3) of this section, and calculate the power loss for each of these basic models; (ii) Test at least five units of each of these basic models in accordance with the applicable test procedure and §429.47, and determine the power loss for each of these basic models; (iii) The predicted total power loss for each of these basic models, calculated by applying the AEDM pursuant to paragraph (d)(2)(i) of this section, must be within plus or minus five percent of the mean total power loss determined from the testing of that basic model pursuant to paragraph (d)(2)(ii) of this section; and (iv) Calculate for each of these basic models the percentage that its power loss calculated pursuant to paragraph (d)(2)(i) of this section is of its power loss determined from testing pursuant to paragraph (d)(2)(ii) of this section, compute the average of these percentages, and that calculated average power loss, expressed as a percentage of the average power loss determined from testing, must be no less than 97 percent and no greater than 103 percent. (3) Additional testing requirements. (i) A manufacturer must select basic models for testing in accordance with the following criteria: (A) Two of the basic models must be among the five basic models with the highest unit volumes of production by the manufacturer in the prior year, or during the prior 12calendarmonth period beginning in 2003,1 whichever is later; 1When identifying these five basic models, any basic model that does not comply with Federal energy conservation standards for distribution transformers that may be in effect shall be excluded from consideration. (B) No two basic models should have the same combination of power and voltage ratings; and (C) At least one basic model should be singlephase and at least one should be threephase. (ii) In any instance where it is impossible for a manufacturer to select basic models for testing in accordance with all of these criteria, the criteria shall be given priority in the order in which they are listed. Within the limits imposed by the criteria, basic models shall be selected randomly. (4) Subsequent verification of an AEDM. (i) Each manufacturer that has used an AEDM under this section shall have available for inspection by the Department of Energy records showing: (A) The method or methods used; (B) The mathematical model, the engineering or statistical analysis, computer simulation or modeling, and other analytic evaluation of performance data on which the AEDM is based; (C) Complete test data, product information, and related information that the manufacturer has generated or acquired pursuant to paragraph (d)(4) of this section; and (D) The calculations used to determine the efficiency and total power losses of each basic model to which the AEDM was applied. (ii) If requested by the Department, the manufacturer must perform at least one of the following: (A) Conduct simulations to predict the performance of particular basic models of distribution transformers specified by the Department; (B) Provide analyses of previous simulations conducted by the manufacturer; (C) Conduct sample testing of basic models selected by the Department; or (D) Conduct a combination of these. (e) Alternate Rating Method (ARM) for residential splitsystem central air conditioners and heat pumps— (1) Criteria an ARM must satisfy. The basis of the ARM referred to in §429.16(a)(2)(ii) for residential central air conditioners and heat pumps must be a representation of the test data and calculations of a mechanical vaporcompression refrigeration cycle. The major components in the refrigeration cycle must be modeled as “fits” to manufacturer performance data or by graphical or tabular performance data. Heat transfer characteristics of coils may be modeled as a function of face area, number of rows, fins per inch, refrigerant circuitry, airflow rate and enteringair enthalpy. Additional performancerelated characteristics to be considered may include type of expansion device, refrigerant flow rate through the expansion device, power of the indoor fan and cyclicdegradation coefficient. Ratings for untested combinations must be derived from the ratings of a combination tested in accordance with §429.16(a)(2)(i). The seasonal energy efficiency ratio (SEER) and/or heating seasonal performance factor (HSPF) ratings for an untested combination must be set equal to or less than the lower of the SEER and/or HSPF calculated using the applicable DOEapproved alternative rating method (ARM). If the method includes an ARM/simulation adjustment factor(s), determine the value(s) of the factors(s) that yield the best match between the SEER/HSPF determined using the ARM versus the SEER/HSPF determined from testing in accordance with §429.16(a)(2)(i). Thereafter, apply the ARM using the derived adjustment factor(s) only when determining the ratings for untested combinations having the same outdoor unit. (2) Approval of an ARM. (i) Manufacturers who elect to use an ARM for determining measures of energy consumption under §429.16(a)(2)(ii)(B)(1) and paragraph (e)(1) of this section must submit a request for DOE to review the ARM. Send the request to: U.S. Department of Energy, Office of Energy Efficiency and Renewable Energy, Building Technologies Program (EE2J), Attention: Alternative Rating Methods (ARM) for Certification and Compliance, Forrestal Building, 1000 Independence Avenue, SW., Washington, DC 205850121. (ii) Each request to DOE for approval of an ARM must include: (A) The name, mailing address, telephone number, and email address of the official representing the manufacturer. (B) Complete documentation of the alternative rating method to allow DOE to evaluate its technical adequacy. The documentation must include a description of the methodology, state any underlying assumptions, and explain any correlations. The documentation should address how the method accounts for the cyclicdegradation coefficient, the type of expansion device, and, if applicable, the indoor fanoff delay. The requestor must submit any computer programs—including spreadsheets—having less than 200 executable lines that implement the ARM. Longer computer programs must be identified and sufficiently explained, as specified above, but their inclusion in the initial submittal package is optional. Applicability or limitations of the ARM (e.g., only covers singlespeed units when operating in the cooling mode, covers units with rated capacities of 3 tons or less, not applicable to the manufacturer's product line of nonducted systems) must be stated in the documentation. (C) Complete test data from laboratory tests on four mixed (i.e., nonhighestsalesvolume combination) systems per each ARM. (1) The four mixed systems must include four different indoor units and at least two different outdoor units. A particular model of outdoor unit may be tested with up to two of the four indoor units. The four systems must include two lowcapacity mixed systems and two highcapacity mixed systems. The lowcapacity mixed systems may have any capacity. The rated capacity of each highcapacity mixed system must be at least a factor of two higher than its counterpart lowcapacity mixed system. The four mixed systems must meet the applicable energy conservation standard in §430.32(c) in effect at the time of the rating. (2) The four indoor units must come from at least two different coil families, with a maximum of two indoor units coming from the same coil family. Data for two indoor units from the same coil family, if submitted, must come from testing with one of the “lowcapacity mixed systems” and one of the “highcapacity mixed systems.” A mixed system indoor coil may come from the same coil family as the highestsalesvolumecombination indoor unit (i.e., the “matched” indoor unit) for the particular outdoor unit. Data on mixed systems where the indoor unit is now obsolete will be accepted towards the ARMvalidation submittal requirement if it is from the same coil family as other indoor units still in production. (3) The first two sentences of paragraph (e)(2)(ii)(C)(2) of this section do not apply if the manufacturer offers indoor units from only one coil family. In this case only, all four indoor coils must be selected from this one coil family. If approved, the ARM will be specifically limited to applications for this one coil family. (D) All product information on each mixed system indoor unit, each matched system indoor unit, and each outdoor unit needed to implement the proposed ARM. The calculated ratings for the four mixed systems, as determined using the proposed ARM, must be provided along with any other related information that will aid the verification process. (E) If request for approval is for an updated ARM, manufacturers must identify modifications made to the ARM since the last submittal, including any ARM/simulation adjustment factor(s) added since the ARM was last approved by DOE. (iii) Approval must be received from the Department to use the ARM before the ARM may be used for rating splitsystem central air conditioners and heat pumps. If a manufacturer has a DOEapproved ARM for products also distributed in commerce by a private labeler, the ARM may also be used by the private labeler for rating these products. Once an ARM is approved, DOE may contact a manufacturer to learn if their ARM has been modified in any way and to verify that the ARM is being applied as approved. DOE will give followup priority to individual combinations having questionably high ratings (e.g., a coilonly system having a rating that exceeds the rating of a coilonly highest sales volume combination by more than 6 percent). (3) Changes to DOE's regulations requiring reapproval of an ARM. Manufacturers who elect to use an ARM for determining measures of energy consumption under §429.16(a)(2)(ii)(B)(1) and paragraph (e)(1) of this section must submit a request for DOE to review the ARM when: (i) DOE amends the energy conservation standards as specified in §430.32 for residential central air conditioners and heat pumps. In this case, any testing and evidence required under paragraph (e)(2) of this section shall be developed with units that meet the amended energy conservation standards specified in §430.32. Reapproval for the ARM must be obtained before the compliance date of amended energy conservation standards. (ii) DOE amends the test procedure for residential air conditioners and heat pumps as specified in appendix M to subpart B of part 430. Reapproval for the ARM must be obtained before the compliance date of amended test procedures. (4) Manufacturers that elect to use an ARM for determining measures of energy consumption under §429.16(a)(2)(ii)(B)(1) and paragraph (e)(1) of this section must regularly either subject a sample of their units to independent testing, e.g., through a voluntary certification program, in accordance with the applicable DOE test procedure, or have the representations reviewed by an independent stateregistered professional engineer who is not an employee of the manufacturer. The manufacturer may continue to use the ARM only if the testing establishes, or the registered professional engineer certifies, that the results of the ARM accurately represent the energy consumption of the unit(s). Any proposed change to the alternative rating method must be approved by DOE prior to its use for rating. (5) Manufacturers who choose to use computer simulation or engineering analysis for determining measures of energy consumption under §429.16(a)(2)(ii)(B)(1) and paragraphs (e)(1) through (e)(4) of this section must permit representatives of the Department of Energy to inspect for verification purposes the simulation method(s) and computer program(s) used. This inspection may include conducting simulations to predict the performance of particular outdoor unit “indoor” unit combinations specified by DOE, analysis of previous simulations conducted by the manufacturer, or both. (f) Alternative efficiency determination method (AEDM) for walkin refrigeration equipment— (1) Criteria an AEDM must satisfy. A manufacturer may not apply an AEDM to a basic model to determine its efficiency pursuant to this section unless: (i) The AEDM is derived from a mathematical model that estimates the energy efficiency or energy consumption characteristics of the basic model as measured by the applicable DOE test procedure; (ii) The AEDM is based on engineering or statistical analysis, computer simulation or modeling, or other analytical evaluation of performance data; and (iii) The manufacturer has validated the AEDM, in accordance with paragraph (f)(2) of this section. (2) Validation of an AEDM. Before using an AEDM, the manufacturer must validate the AEDM's accuracy and reliability as follows: (i) The manufacturer must select at least the minimum number of basic models for each validation class specified in paragraph (f)(2)(iv) of this section to which the particular AEDM applies. Test a single unit of each basic model in accordance with paragraph (f)(2)(iii) of this section. Using the AEDM, calculate the energy use or energy efficiency for each of the selected basic models. Compare the results from the single unit test and the AEDM output according to paragraph (f)(2)(ii) of this section. The manufacturer is responsible for ensuring the accuracy and repeatability of the AEDM. (ii) Individual model tolerances. (A) The predicted efficiency for each model calculated by applying the AEDM may not be more than five percent greater than the efficiency determined from the corresponding test of the model. (B) The predicted energy efficiency for each model calculated by applying the AEDM must meet or exceed the applicable federal energy conservation standard. (iii) Additional test unit requirements. (A) Each AEDM must be supported by test data obtained from physical tests of current models; and (B) Test results used to validate the AEDM must meet or exceed current, applicable Federal standards as specified in part 431 of this chapter; (C) Each test must have been performed in accordance with the applicable DOE test procedure with which compliance is required at the time the basic model is distributed in commerce; and (D) For rating WICF refrigeration system components, an AEDM may not simulate or model portions of the system that are not required to be tested by the DOE test procedure. That is, if the test results used to validate the AEDM are for either a unit cooler only or a condensing unit only, the AEDM must estimate the system rating using the nominal values specified in the DOE test procedure for the other part of the refrigeration system. (iv) WICF refrigeration validation classes.
^{1}AEDMs validated for dedicated condensing, medium temperature, outdoor systems may be used to determine representative values for dedicated condensing, medium temperature, indoor systems, and additional validation testing is not required. AEDMs validated for only dedicated condensing, medium temperature, indoor systems may not be used to determine representative values for dedicated condensing, medium temperature, outdoor systems. ^{2}AEDMs validated for dedicated condensing, low temperature, outdoor systems may be used to determine representative values for dedicated condensing, low temperature, indoor systems, and additional validation testing is not required. AEDMs validated for only dedicated condensing, low temperature, indoor systems may not be used to determine representative values for dedicated condensing, low temperature, outdoor systems. ^{3}AEDMs validated for medium temperature, outdoor condensing units may be used to determine representative values for medium temperature, indoor condensing units, and additional validation testing is not required. AEDMs validated for only medium temperature, indoor condensing units may not be used to determine representative values for medium temperature, outdoor condensing units. ^{4}AEDMs validated for low temperature, outdoor condensing units may be used to determine representative values for low temperature, indoor condensing units, and additional validation testing is not required. AEDMs validated for only low temperature, indoor condensing units may not be used to determine representative values for low temperature, outdoor condensing units. (3) AEDM records retention requirements. If a manufacturer has used an AEDM to determine representative values pursuant to this section, the manufacturer must have available upon request for inspection by the Department records showing: (i) The AEDM, including the mathematical model, the engineering or statistical analysis, and/or computer simulation or modeling that is the basis of the AEDM; (ii) Equipment information, complete test data, AEDM calculations, and the statistical comparisons from the units tested that were used to validate the AEDM pursuant to paragraph (f)(2) of this section; and (iii) Equipment information and AEDM calculations for each basic model to which the AEDM has been applied. (4) Additional AEDM requirements. If requested by the Department the manufacturer must perform at least one of the following: (i) Conduct simulations before representatives of the Department to predict the performance of particular basic models of the product to which the AEDM was applied; (ii) Provide analyses of previous simulations conducted by the manufacturer; or (iii) Conduct certification testing of basic models selected by the Department. (5) AEDM verification testing. DOE may use the test data for a given individual model generated pursuant to §429.104 to verify the certified rating determined by an AEDM as long as the following process is followed: (i) Selection of units. DOE will obtain units for test from retail, where available. If units cannot be obtained from retail, DOE will request that a unit be provided by the manufacturer. (ii) Lab requirements. DOE will conduct testing at an independent, thirdparty testing facility of its choosing. In cases where no thirdparty laboratory is capable of testing the equipment, it may be tested at a manufacturer's facility upon DOE's request. (iii) Manufacturer participation. Testing will be performed without manufacturer representatives onsite. (iv) Testing. All verification testing will be conducted in accordance with the applicable DOE test procedure, as well as each of the following to the extent that they apply: (A) Any active test procedure waivers that have been granted for the basic model; (B) Any test procedure guidance that has been issued by DOE; (C) If during test setup or testing, the lab indicates to DOE that it needs additional information regarding a given basic model in order to test in accordance with the applicable DOE test procedure, DOE may organize a meeting between DOE, the manufacturer and the lab to provide such information. (D) At no time during the process may the lab communicate directly with the manufacturer without DOE present. (v) Failure to meet certified rating. If a model tests worse than its certified rating by an amount exceeding the tolerance prescribed in paragraph (f)(5)(vi) of this section, DOE will notify the manufacturer. DOE will provide the manufacturer with all documentation related to the test set up, test conditions, and test results for the unit. Within the timeframe allotted by DOE, the manufacturer may then present all claims regarding testing validity. (vi) Tolerances. for efficiency metrics, the result from a DOE verification test must be greater than or equal to the certified rating × (1 − the applicable tolerance).
(vii) Invalid rating. If, following discussions with the manufacturer and a retest where applicable, DOE determines that the testing was conducted appropriately in accordance with the DOE test procedure, the rating for the model will be considered invalid. Pursuant to 10 CFR 429.13(b), DOE may require a manufacturer to conduct additional testing as a remedial measure. [76 FR 12451, Mar. 7, 2011; 76 FR 24780, May 2, 2011, as amended at 78 FR 79595, Dec. 31, 2013; 79 FR 25505, May 5, 2014; 79 FR 27410, May 13, 2014; 80 FR 152, Jan. 5, 2015] §429.71 Maintenance of records.(a) The manufacturer of any covered product or covered equipment shall establish, maintain, and retain the records of certification reports, of the underlying test data for all certification testing, and of any other testing conducted to satisfy the requirements of this part, part 430, and part 431. Any manufacturer who chooses to use an alternative method for determining energy efficiency or energy use in accordance with §429.70 must retain the records required by that section, any other records of any testing performed to support the use of the alternative method, and any certifications required by that section, on file for review by DOE for two years following the discontinuance of all models or combinations whose ratings were based on the alternative method. (b) Such records shall be organized and indexed in a fashion that makes them readily accessible for review by DOE upon request. (c) The records shall be retained by the manufacturer for a period of two years from the date that the manufacturer or third party submitter has notified DOE that the model has been discontinued in commerce. §429.72 Alternative methods for determining nonenergy ratings.(a) General. Where §429.14 through §429.54 authorize the use of an alternative method for determining a physical or operating characteristic other than the energy consumption or efficiency, such characteristics must be determined either by testing in accordance with the applicable test procedure and applying the specified sampling plan provisions established in those sections or as described in the appropriate productspecific paragraph below. In all cases, the computeraided design (CAD) models, measurements, and calculations used to determine the rating for the physical or operating characteristic shall be retained as part of the test records underlying the certification of the basic model in accordance with §429.71. (b) Testing. [Reserved] (c) Residential refrigerators, refrigeratorfreezers, and freezers. The total refrigerated volume of a basic model of refrigerator, refrigeratorfreezer, or freezer may be determined by performing a calculation of the volume based upon computeraided design (CAD) models of the basic model in lieu of physical measurements of a production unit of the basic model. Any value of total refrigerated volume of a basic model reported to DOE in a certification of compliance in accordance with §429.14(b)(2) must be calculated using the CADderived volume(s) and the applicable provisions in the test procedures in 10 CFR part 430 for measuring volume, and must be within two percent, or 0.5 cubic feet (0.2 cubic feet for compact products), whichever is greater, of the volume of a production unit of the basic model measured in accordance with the applicable test procedure in 10 CFR part 430. [79 FR 22348, Apr. 21, 2014] Appendix A to Subpart B of Part 429—Student's tDistribution Values for Certification TestingFigure 1—tDistribution Values for Certification Testing [OneSided]
[76 FR 12451, Mar. 7, 2011; 76 FR 24780, May 2, 2011]
